How to Test a Water Heater Element
An Overview of the Process of Testing a Water Heater Element
- The following tools are required: a screwdriver, a digital multimeter, and a non-contact voltage tester (optional). Step 1: Turn off the power. Step 2: Take off the metal covering. Step 3: Remove the insulation from the house. Step 4: Set the heating element in its proper location. Step 5: Make sure the electricity is turned off. Step 6: Use a multimeter to inspect the element. Step 7: Assemble the water heater again.
One of the most typical reasons for your water heater not to be generating hot water is a defective heating element, which is one of several probable causes. However, checking the heating element is one of the most straightforward diagnostic procedures you can perform on your own. It is not necessary to drain the tank or to interfere with any gas, water, or electrical lines. This Might Also Be of Interest to You: What is the procedure for turning on my water heater? To determine whether the heating element is to blame for your water heater’s problems before spending a lot of money on expert repair — or even complete replacement — follow these simple procedures.
Signs of a Bad Water Heater Element
Even if it is simple to test the element, it is a good idea to be familiar with the most typical indicators of a malfunctioning heater element in order to assess whether or not testing is even necessary. The following are signs of a faulty heating element:
- Water that is lukewarm
- The amount of hot water is little. There is no hot water. The hot water runs out more quickly than normal
- The circuit breaker for the water heater is continually tripping
Drinking water that is just warm enough The volume of hot water is little, a lack of heat in the house; It takes longer for hot water to run out than normal. The circuit breaker for the water heater keeps tripping.
Symptoms of a Bad Upper Heating Element:
- There is no hot water. The temperature of the hot water does not reach the setting on the thermostat
Symptoms of a Bad Lower Heating Element:
- A small amount of hot water
- The hot water runs out more quickly than normal
Minimal hot water available, and it depletes more quickly than usual.
- Screwdriver, digital multimeter, non-contact voltage tester (optional), and a pair of safety glasses
How to Test the Element
The fact that testing the heater element entails dealing with electricity means that you must first shut down your water heater to guarantee that you are operating in a safe environment. To accomplish this, you must first turn off the circuit breaker that supplies electricity to the water heater. Circuit breakers are placed in your home’s central breaker box, which is often found in the garage, basement, or beneath a stairwell. It is a 1-foot by 2-foot metal box with a breaker on each side. The electrician who wired your property should have clearly designated the breaker that serves your water heater, which should be located within the breaker box.
If the breaker isn’t labeled, you may either cut off the electricity to your entire house with the main breaker (which is normally placed at the top of the box) or turn off all of the double breakers, which are breakers that are linked together with another breaker.
Step 2. Remove the Metal Covers
On the side of your water heater, there should be one or two metal plate covers to protect it from the elements. They are secured in place by two or more screws with Phillips heads, which are commonly found on these covers. They house the thermostat and heating element. These screws can be removed using a screwdriver or a power drill equipped with the proper bit.
Step 3. Remove the Insulation and Plastic Covers
Most water heaters feature an insulating layer between the metal cover and the heating element, as well as a thin plastic barrier between the two. Rigid foam insulation or flexible fiberglass insulation are also options for insulation. You should be able to remove foam insulation by hand in one piece in most circumstances, but in certain cases it may be necessary to pry or cut it out. With a utility knife, carefully cut away any fiberglass insulation that has been trapped. It is common for the plastic shield to be clipped onto metal tabs on the water heater.
Following light to moderate pressure, it should pop out of the way and be removed. It is important not to damage any of these components, since they will be reinserted when your test has been successfully finished.
Step 4. Locate the Heating Element
The thermostat and heating element should be visible at this point in the process. The thermostat is typically rectangular in shape, with multiple electrical wires running through it and connecting to screws on either side of it. It’s situated just above the heating element, as the name implies. The heating element itself is contained within the tank. The visible piece is the approximately 1-inch square base (or “end point”), which is held together by two screws that are connected to the electrical lines.
Additional Related Articles:
- How to Relight the Pilot Light on Your Water Heater
- Don’t Forget to Flush the System! The following is a 6-Step Guide for Flushing Your Gas or Electric Water Heater: Is it possible to work without a tank? Determine whether or not a tankless water heater is appropriate for your home. What is a Smart Water Heater and how does it work? When your water heater isn’t working, you’ll notice these seven tell-tale signs.
Step 5. Verify the Electricity Is Off
Using a non-contact voltage tester or a multimeter, confirm that the power has been turned off. A non-contact voltage tester is a pen-shaped gadget that illuminates or emits a beep when it comes into close proximity to an electrically charged (“live”) wire or other live wire. In order to identify if the electricity is turned off, it only has to be put near the electrical cables that connect the thermostat and heating element. If it continues to light up or beep, this indicates that the cables are still live and that the energy has not been fully turned off.
Any electrical activity should not be recorded in your logs.
After moving the probes around, repeat the testing.
This will assist you in ensuring that you are receiving a trustworthy reading.
Step 6. Check the Heater Element With Your Multimeter
Generally speaking, the functioning of a heating element is governed by the resistance present in the circuit, which is measured in ohms (). Adjust the ohms setting on your multimeter to the lowest possible value. Touch the center of one of the heating element screws with the red probe, and the center of the other screw with the black probe. When measuring resistance, it makes no difference which probe is in contact with which screw. In order to determine whether or not the heating element is functioning properly, your multimeter should read anywhere between 10 and 30.
If your water heater has two heating elements, repeat this procedure on the other heating element.
Step 7. Reassemble the Water Heater
Irrespective of whether or not your heating elements are in excellent operating order, it’s time to reassemble your water heater. Replace the plastic cover over the heating element (if one is present), as well as the insulation, if necessary.
Finally, re-energize the circuit breaker for the water heater. Depending on whether you changed a heater element or not, you may have to wait a few hours for the water to heat up before determining whether your repair was effective.
Test & Replace a Bad Water Heating Element: DIY Guide
When you discover that you have no hot water in your house, it may be really annoying. Despite the fact that hot water is a crucial component of our everyday life, we sometimes take for granted that it will always be available. In the event that a water heater’s heating element or thermostat fails, the most likely reason is a faulty heating element or thermostat. So, what is the best way to test a faulty heating element? Turn off the water heater’s electricity and take off the covers over the heating components before continuing.
Continuity refers to the fact that there is no interruption in the flow of electricity between two connecting points.
Let us first explain how the heating components function, as well as some other possible causes of your lack of hot water, as well as how water heaters are designed to work.
How Dual Heating Elements Work
When it comes to electric water heaters, there are normally two heating elements: the bottom heating element and the higher heating element. Each heating element is equipped with a thermostat, which regulates the temperature of the heating element. When the water heater is sluggish to heat up or runs out of hot water more quickly than normal, the bottom element is almost often the cause of the problem. If, on the other hand, the water heater is not producing any hot water, the fault is most likely with the higher element.
The reason for this is that the thermostat linked to the top element also regulates electricity to the lower thermostat and heating element on the lower end of the heating system.
How to test water heater elements with a multimeter and a continuity tester will be covered in the remainder of this article.
Troubleshooting the Water Heater
Consider some of the other typical reasons of water heater malfunction before concluding that one of the heating components is to blame for your water heater’s inability to provide hot water. For starters, check to determine whether any circuit breakers in the electrical panel box have been triggered. It is possible for a water heater’s breaker to trip for a variety of reasons. If your water heater’s circuit breaker has tripped, try turning it to the OFF position and then back to the ON position to see if it can be reset.
- A heating element that has failed
- A thermostat that is not working properly
- A short circuit in the electrical wire circuit
It is necessary to inspect both parts of the heater if the circuit breaker is constantly tripped. Electrical connections that are loose or broken can also cause a breaker to trip; in this case, search for burned or melted wires at the circuit breaker or the electrical connections at the top of the water heater.
Resetting the water heater is an alternative approach. How to go about it is as follows:
- It is necessary to examine both parts of the heater if the circuit breaker is continually tripped. Electrical connections that are loose or defective can also cause a breaker to trip
- In this case, search for burnt or melted wires at the circuit breaker or at the electrical connections at the top of the water heater. Resetting the water heater is an other option to consider. Follow these steps to accomplish your goals:
It is possible that the thermostat in either the top or lower element is malfunctioning if the reset button trips and won’t return to its original position.
How an Electric Water Heater Works
Electric water heaters are deceptively easy appliances to operate. A conventional electric heater control circuit consists of two heating elements, an upper thermostat, a lower thermostat, wires, and a high-limit switch with a reset button. Other components include an upper thermostat and a lower thermostat. The thermostats, to which each element is attached, are in charge of controlling the two components. Depending on the kind of water heater, the temperature of thethermostats can be adjusted by the user manually.
- And, of course, the higher the temperature is set, the more electricity is consumed by the system.
- Running both elements at the same time may void any warranty that may have been provided by the water heater manufacturer.
- If the components are not entirely submerged in water, they are at risk of catching fire.
- The higher thermostat, when the top of the tank reaches a certain temperature, shuts down the upper element and sends power to the lower thermostat, which in turn switches on the bottom element.
- The lower element regulates the temperature of the tank by cycling on and off at regular intervals throughout the day and night.
- Cold water quickly fills the bottom of the tank when hot water is pulled from the tank through the dip tube.
- It is only when it reaches the top third that the bottom element is turned off and the upper element is activated.
- Modern water heaters will automatically switch to standby mode after the temperature of the water has been reached.
- Modern water heaters only need to be used for roughly 2 hours every day on average.
How to Test Water Heater Elements
You can use a non-contact voltage tester or a multimeter to assess whether or not the heating elements have failed in your vehicle.
When working with a multimeter, you must understand how to interpret the results. Tools You’ll need the following supplies:
- A non-contact voltage tester, a screwdriver, a multimeter, and a continuity tester are all useful tools.
Step 1: Disconnect the electricity from the circuit breaker. It is positioned within the main electrical panel, near the circuit breaker. Electric water heaters are commonly equipped with a double breaker rated at 30 amps. See if there is a breaker labeled “Water Heater.” If your circuit breakers are not correctly labeled, you may need to hire an electrician to properly label the circuit breakers for you. The top and lower side panels of the water heater should be opened in step two. Two panels can be installed on the side of a normal 40-gallon or larger water heater tank to provide additional protection from the elements.
- Remove the screws that are holding the panels in place and lay them away in a secure location until the job is finished.
- It is dependent on the age of the water heater that the insulating material used varies from one water heater to another.
- Dealing with foam can be difficult, thus it will almost certainly be essential to reduce its thickness.
- You will see a plastic cover over the thermostat and heating element after the insulation has been removed.
- Remove the plastic covering in order to reveal the thermostats and heating components beneath it.
- This step is required for safety reasons in order to establish that there is no electricity to the heating components (if you turned off the wrong breaker).
- If the tester flashes frequently, as if it were an alarm, this indicates that voltage is present.
- Step 6: Disconnect the element wiresCheck to verify if any of the wires are charred or melted before proceeding forward.
- When a burnt or melted wire is discovered, the component should be replaced.
- To check for continuity, you may use either a continuity tester or a multimeter.
- There are three major methods in which you may make use of a continuity tester:
- Connect the alligator clip to one of the element screws and the probe to the other screw using the alligator clip. A malfunctioning element is indicated by a tester that does not light up, buzzes, or reacts just minimally. Touch each screw to the bare metal section of the water heater, following the same process as before. Touch each screw to the metal base of the element, following the same process as before.
If the elements fail to pass all three tests, they are deemed defective and must be replaced with new ones. As opposed to the continuity tester, a multimeter is more difficult to use. It consists of two wire leads with metal probes attached to them, one of which is red and the other black. The first step is to turn the dial on the multimeter to Rx1k (resistance times 1000 ohms). Follow the instructions above to complete all three tests. The tool should detect about 16 ohms for a 3500-watt element when testing both element screws, as stated in test 1, 12-13 ohms for a 4500-watt element, and 10-11 ohms for a 5500-watt element when testing both element screws.
It is necessary to replace the element if you repeat tests 2 and 3 and notice that the multimeter needle moves. If the elements pass all three tests, it is possible that the thermostat is the source of the problem.
How to Replace Water Heater Elements
It is far simpler to replace a heating element than it is to test one. Check to ensure that the replacement has the same voltage as the original. When it comes to wattage, it might either be the same or lower than before. The lower-wattage element tends to survive longer, but it also produces significantly less heat. You’ll require the following tools: You’ll need to empty the water heater before you can replace the heating components. Please refer to our article, Water Heater Maintenance Tips – Gas and Electric Tank Water Heaters, for a detailed step-by-step instruction to draining your water heater.
- Some YouTube videos demonstrate how to change the heating element without having to empty the water heater.
- Draining and cleaning the water heater is another something you should perform once a year to remove sediment from the water heater’s internal tank.
- Take advantage of this chance to do a comprehensive service on your water heating system.
- To loosen the heating element, crank it in a counter-clockwise manner with the heating element wrench until it becomes loose.
- Make certain that the previous seal has been thoroughly removed.
- Examine the sort of heating element that is installed in your water heater.
- To determine the heating element you have, take the old heating element to a home improvement store for comparison.
Inspect and tighten the new seal that comes with the replacement heating element with the heating element wrench to ensure that it is properly sealed.
Make sure that all of the wires are properly connected and that they are snugly secured with the screwdriver.
It is advised that both heating components be replaced at the same time, even if one of them is still in good operating condition.
Step 4: Refill the water heater with fresh water.
The faucet should be closed once the water has been drawn through it.
Step 5: Tighten the panel covers in place.
If the thermostat is exposed to cool air, it has the potential to interfere with the temperature readings on the display screen.
Step 6: Reconnect the electricity to the system.
Do not switch on the electricity until the tank is completely filled with water.
It will take roughly one hour to recover.
Before beginning any job, you should contact with a competent expert and verify that all necessary permits have been obtained.
As an affiliate, HomeInspectionInsider.com participates in a variety of affiliate programs with other websites. Hubert Miles receives a commission for recommending visitors and commerce to these businesses.
DIY Water Heater Testing and Repair
Occasionally, the heating elements on electric water heaters break long before the water heater itself fails, but changing them in a hot water heater is a simple Do It Yourself repair.
The majority of the time, replacing one or both of the heating elements will address the problem if your electric hot water heater is taking a long time to heat up, running out of hot water more quickly than it used to, or not delivering any hot water. Water heater repairs are simple, and replacement components are affordable ($8 to $20), and they are easily accessible at home centers, hardware shops, and appliance parts dealers across the country. How to test the heating elements, remove one if it’s defective, and replace it with a new one will be demonstrated.
If your heater is reaching its end of life, it may be more cost-effective to replace it than to repair it.
Other Causes of Water Not Getting Hot
Of course, there are a variety of additional factors that might contribute to a shortage of hot water. Before you begin testing the elements, double-check that the circuit breaker is not tripped and that it is in the on position. Press the reset button on the high-temperature cutoff, which is positioned slightly above the top thermostat, at the same time. Although resetting either the circuit breaker or the high-temperature cutoff may remedy the problem, the fact that they were tripped in the first place may suggest that there is an electrical fault with the system in the first place.
Assuming that the heating components are working properly, the thermostats or cutoff switch may be defective.
Video: How to Test Your Water Heater Element
- Power should be turned off at the circuit breaker. Remove the metal covers from the thermostats and heating components to reveal them.
- Pro tip: Check that the power has been turned off by tapping the electrical connections with a noncontact voltage detector.
Test the Wires
- Please keep in mind that if the wires are covered by metal conduit, the tester will not read the voltage. Take off the metal thermostat cover that is mounted on the side of the water heater, peel out all of the insulation, and place the tester in close proximity to the wires that go up to the top of the high-temperature cutoff switch.
- Placing the tester against the metal water heater shell will get the following results:
- Note: If the tester does not light up, it is okay to proceed with the testing of the components.
What’s Inside a Water Heater and How It Works
The vast majority of domestic electric water heaters feature two heating elements: one near the top of the tank and another towards the bottom of the tank. After entering the top, power travels to the high-temperature cutoff switch, and then to the thermostats and elements on each side of the unit. The temperature of the top and bottom components is regulated by two different thermostats. When the water at the top of the tank becomes too hot, the top element goes off and the bottom element takes over to heat the water.
Sign Up For Our Newsletter
Complete your do-it-yourself tasks like an expert! Become a subscriber to our newsletter! Do It Right the First Time, and Do It Yourself! Step number three.
Test Continuity for a Burned-Out Element
- Professionally complete your home improvement projects! Become a subscriber to our mailing list! It’s important to do things right the first time. Three-pointed strategy
- Disconnect the wires from the terminal screws using a wire cutter. Attach the alligator clamp to one of the element screws using a hex key. With the tester probe, make contact with the other screw.
- Note: If the tester does not illuminate, the element should be replaced.
Test for a Short Circuit
- The alligator clip should be attached to one of the element screws. Touch the tester probe to the mounting bracket for the element
- Repeat the process on the other screw.
- It is important to note that if the tester light illuminates either time, there is a short. Replace the element with a new one
The Secret of the Red Button
Occasionally, both elements will pass the test, but you will still be unable to receive hot water.
Try pressing the “high-temperature cutoff” button, which is situated right above the upper thermostat, to see if that helps. It may temporarily cure the problem, but if the problem recurs, the heating components should be checked. Step number five.
Remove the Bad Element
- Close the intake valve for cold water
- Start by turning on the hot water tap in the kitchen. Pour water into the tank by connecting a garden hose to the drain valve and opening it
- Close the inlet valve for cold water. In the kitchen, turn on the hot water faucet. Pour water into the tank by connecting a garden hose to the drain valve and opening it.
- Close the cold-water inflow valve. In the kitchen, turn on the hot water faucet
- Drain the tank by connecting a garden hose to the drain valve and turning it on.
- Close the cold-water inflow valve
- Open the hot water faucet in the kitchen
- Connect a garden hose to the drain valve and turn it on to drain the tank.
Install the New Element
- Insert the replacement element into the water heater and tighten it down with the heating element wrench if necessary. Reconnect the wires, checking to see that the connections are secure. Remove the insulation and metal covers and replace them.
Buying Heating Elements
Fitting a new water heater element into the tank and tightening it using a heating element wrench Ensure that the cables are securely connected by tightening the connectors. The insulation and metal coverings should be replaced.
8 Steps to Test Water Heater Element
Have you noticed a significant reduction in the temperature of the water delivered by your water heater? If so, you’re not alone. Every home need hot water in order to do a variety of household tasks. When your water heater, on the other hand, generates lukewarm water that is incapable of serving the intended function, it may be really annoying. While a variety of factors can influence the efficiency with which your water heater operates, a malfunctioning element is one of the most common reasons of water heater failure.
As a result, it is necessary to understand how to test and replace a water heater element.
Have you noticed a significant reduction in the temperature of the water delivered by your water heater? If so, you are not alone. A constant supply of hot water is required in every home to complete a variety of household tasks. But when your water heater produces lukewarm water that is insufficient for the reasons for which it was designed, it may be annoying to say the least. There are a variety of issues that might impair the efficiency of your water heater’s operation, but one of the most common is a malfunctioning element.
As a result, understanding how to inspect and replace a water heater element is essential.
- Hand gloves, a screwdriver, safety goggles, and a digital multimeter are all required.
Causes of Failure of Water Heater Element
There might be several factors contributing to your water heater element not functioning properly.
a). Accumulation of Mineral
As a result of the numerous procedures that they go through in order to provide hot water, water heater elements have a limited operating life. The deteriorated state of these elements is exacerbated if there are mineral deposits present in the water. The minerals are solidified as a result of the ongoing process. Lower elements may get encircled by mineral deposits in some instances, which may finally lead the element to fail. Turning down your water heater and flushing your water heater once a year is an excellent preventative action you may implement.
Check out our earlier post to find out how to cleanse a water heater effectively. If you are able to accomplish this, the sediments will be eliminated and the life of the components will be extended significantly.
b). Trapped Air Pockets
All water heater elements must be operated with their heads submerged in water at all times. If the heat created by an element is not transmitted to the water, it might burn through the copper of the element. A bleed line on the water is required once or twice a year to remove trapped air and sediments from the tank. If this is not done, the trapped air, referred to as “Air Pockets,” will cause the upper element to burn since it is not immersed in water. This has the potential to cause the water heater to fail.
c). Malfunctioning Thermostat
The thermostat’s job is to notify the elements when to heat the water at different temperatures depending on the temperature setting. When the temperature rises over a preset threshold, the high limit switch on the thermostat is activated, and the power is turned off as a result. A faulty thermostat will be unable to regulate the amount of heat provided to the water heater element, resulting in the element finally catching fire.
d). Power Surge
A abrupt rise in voltage, such as that induced by a power surge or lightning, can also cause an element to catch fire and burn. Each element has a certain voltage rating, and any voltage that is higher than the appropriate voltage will cause the element to burn.
e). Breakage of Heating Element
When the heating element within the tank of an electric water heater malfunctions, there may be a loss of hot water. Perhaps the element will catch fire, resulting in the water slowly cooling down. If, on the other hand, there is simply cold water, this indicates that the second element has failed. Aside from these three possibilities, a tripped circuit or a blown fuse might also cause the heating element to trip. It is also expected that the fuse box would be checked in this respect.
f). Bad Wire Connection
When the heating element within the tank of an electric water heater fails, there may be a temporary loss of hot water. Possible outcomes include the element being destroyed and the water slowly cooling. If, on the other hand, there is only cold water, this indicates that the second element is not working. It is possible that the heating element will trip for reasons other than the ones listed above, such as a tripped circuit or a blown fuse. In this regard, it is also expected that the fuse box would be checked.
Steps on How to Test Water Heater Element
The following are the methods to be followed when testing for the water element:
Step 1: Disconnect from the power source
This is an extremely important phase in the testing of the water element. You can find the circuit breaker that links your water heater at the main electrical panel. Most of the time, it is located in the metal box that is fastened to the wall. The majority of electricians label each circuit breaker with the name of the device it powers. You’ve found the one that says “hot water heater” and you’ve turned that one off. If you are unsure of which circuit breaker is responsible for your water heater, simply turn off the entire power supply to safeguard your own safety.
Step 2: Open the metal box cover
To open the box, flip the metal lid to the open position. In this location, you will observe the panels that are secured to the water heater’s side by means of screws.
Depending on their size, most water heaters are equipped with one or two panels, respectively. Using a Philips head screwdriver, unscrew the metal plate from the wall. Make certain that the screws do not fall off and land in awkward spots throughout your property.
Step 3: Detach the insulation
Depending on how old your water heater is, a layer of cellulose or fiberglass insulation will be installed behind the metal cover. Disconnect the insulation and place it to one side. While removing the insulation, make use of your safety gloves and goggles. Check to check if the thermostat is protected by a plastic cover. Pulling off the tab on the thermostat plastic cover will also allow you to remove it. However, because some thermostats do not come with a detachable plastic cover, doing this operation is entirely optional.
Step 4: Confirm that the power is off
You should check to make sure that the power has been turned off once more. Install a noncontact voltage detector next to the wire that connects the element to the thermostat to detect voltage fluctuations. The presence of a beeping sound or flashing lights from the voltage detector shows that the water heater is still connected to the electric source. As a precaution, make sure that the power has been entirely turned off before continuing with the task.
Step 5: Locate the endpoint of the elements in the open panel
A single or two elements will most likely be used in your water heater, depending on the size of your residence. Because they extend deep into the water heater’s open panel, you can’t see the elements themselves. You will be able to observe their endpoints, on the other hand. An element measures around 1 inch in length and is fastened to a plastic plate with the use of screws.
Step 6: Note the reading of your water heater element
Set the multimeter dial to the lowest setting, which is Rx1k, which is resistances multiplied by 1000. You should pay attention to the base of your water heater tank. You will notice the wattage and ohms that have been imprinted. With a 3500-watt water heater, the multimeter will read 16, whereas a water heater with a 4,500-watt capacity will read between 12 and 13. You will receive between 10 and 11 cents for a water heater with a 5,500-watt element.
Step 7: Use a digital multimeter to read the water heater element
One of the multimeter probes should be placed on a screw that is connected to the face of the element. This can be accomplished by untangling the loose end of the metal component. Because there are no terminals on the water heater element, you won’t have to worry about which one to test first. Make certain, however, that you are just testing the element itself and not any of the other electrical components that are connected to the element. Connect the prongs of the multimeter to the tip of the element screw with a crimping tool.
If they do not, repeat the process.
This video will demonstrate how to use a digital multimeter if you are unfamiliar with the method.
You should also double-check the reading for the second water heater element.
Step 8: Reattach the disconnected parts
Reattach the wire to the surface of the water heater’s heating components. As well as that, cover the exposed panel with plastic and use the plastic to cover the thermostat.
Tighten the replacement wire and reinsert the screws that had been loose. Reinstall the insulation and switch on the circuit breaker to complete the repair. If you replace a defective element, you will have to wait a few minutes for the water to get to a boiling temperature.
How to Replace an Electric Water Heater Heating Element
The process of replacing a water heater element is rather straightforward. You may learn how to achieve this by watching the video below.
Now that you’ve learned how to test the water heater element, you should be able to solve any issues that arise with this important piece of household equipment. Please keep in mind that you simply need to follow the following procedures:
- Knowing how to test the water heater element, you should be able to solve any problems that may arise with this important piece of household equipment in the future. Remember, all you have to do is follow the steps outlined below.
Any specific questions you have about how to test the water heater element that have not been addressed in this article should be posted in the comment area below. Thanks for reading! Our team is here to assist you with any inquiry. Also, please feel free to forward this post to your friends on any social networking site you like.
How to Test a Water Heater Element
The water heater in your home is one of the most important conveniences in life. If you have ever had to take a cold shower in January, you will understand what I am talking about. A faulty element in your water heater might prevent you from enjoying this convenience. Generally speaking, if your water heater is not working, the element is something you should look at. Many homeowners do not have the necessary tools, nor do they understand how to test a water heater element. Fortunately, all you need is an inexpensive multimeter (try theUEI UTL33T), a screwdriver, and a little bit of information to get started.
How to Check a Water Heater Element
In most cases, a tank water heater will contain two heating components. Before you may test the element, you must first turn off the water heater’s electricity:
- Turn off the power by flipping the appropriate breaker so that no energy is sent to the water heater
- Preparing the multimeter for the water heater’s 240 volts is important since the water heater has two 120 volt cables connected to it, so you’ll want to make sure your multimeter is set up for that voltage. If you do not, you run the danger of harming this delicate instrument. Make contact with one of the element screws with one of the multimeter probes. Using the other probe, connect it to the water heater tank to ground it. If you receive a reading on either connection, the power has not been properly unplugged. If you get a reading on either connection, the power has been properly disconnected. You must first find and turn off the appropriate circuit breaker before proceeding.
Testing a Water Heater Element in 5 Steps
You are now ready to put the water heater to the test after making certain that there is no electricity running to it. It’s important to remember that a water heater typically has two heating components.
- RX1K should be selected on the multimeter. When you press the probes together, the needle on the multimeter should begin to move. Removing the wires from the element requires first loosening the screws, followed by removal of the wiring. Touch the probes to the screws on each element – you want to touch each screw at the same time if possible. It is possible that the element is not functioning if there is no activity with the multimeter needle. With this test, you may occasionally receive a false negative result. Just because there was activity with the needle does not necessarily imply that you need to replace your water heater element with another. You can have a grounded quality to your personality. Test for a grounded element by touching one of the screws with a probe and then contacting the other probe to a metal portion of the water heater tank, as shown in the illustration. If you see movement, this indicates that the element is grounded and has to be replaced.
If your element is grounded, it has the potential to overheat the water and cause the high limit switch to trip, resulting in the water heater’s function being halted completely. If your water heater isn’t operating properly, you may need to reset it. Before you replace anything, give it a go.
Bad Water Heater Element Symptoms
As previously said, the most visible indicator is that the water is extremely cold. This might signify a number of various things at this point. It does not necessary imply that the element is harmful, but it is the most likely method of identifying a concern.
Get Help with All Your Plumbing Problems
More information may be found in this Wiki article: Heating Elements. When you pick PlumbersStock.com, you are choosing a company with years of industry knowledge and goods that are dependable. Please get in touch with us if you have any queries regarding your DIY project or our brands (Bradford White, Takagi, Stiebel Eltron, etc.). Water heater accessories and replacement components are available at discounted prices. Resources that are related to this topic include: How to Replace a Thermocouple (with Pictures) How to Replace the Element in a Water Heater Instructions on How to Clean a Thermocouple How to Replace the Thermostat on a Water Heater The T P Valve Continues to Open Replacement of the T P Valve How to Repair a Water Heater That Is Leaking
how to test the heating elements or electrodes
- See the following Wikipedia page for further information: Heating Element. Choosing PlumbersStock.com means choosing a company with years of business expertise and goods that are trustworthy. For any queries regarding your DIY project or our brands, please do not hesitate to contact us! (Bradford White, Takagi, Stiebel Eltron, etc.). Water heater accessories and replacement components are available at a discounted price. Further information may be found at the following links: Changing a Thermocouple: What You Should Know Changing the Element in a Water Heater Using a Thermocouple, you can clean it. Replacement of the Thermostat on a Water Heater It is necessary to keep the T P valve open. Replacement of the T P valve How to Repair a Water Heater That Is Having Problems
InspectAPedia does not allow any form of conflict of interest. The sponsors, goods, and services described on this website are not affiliated with us in any way. Testing an electric water heater heating element: This article discusses how to test an electric water heater heating element and what readings to anticipate if you are using an ohmmeter to do so. A guide to replacing a defective heating element in an electric hot water heater is provided in this article, which covers the measures to take while checking the heating elements.
The pages on this website will address the vast majority of your queries concerning electrical water heaters, as well as many other issues related to the inspection and repair of building plumbing systems.
For this topic, we also have anARTICLE INDEX available, or you may check the top or bottom of the page.
How to Test Electric Water Heater Heating Elements
Note: Once you have determined which heating element is faulty, you should also refer to REPLACEMENT OF ELECTRIC WATER HEATER ELEMENT. Because the electric water heater may be unable to function owing to a loss of electrical power to the device or a faulty high-temperature cutoff switch, you should also review the test procedures at the bottom of this page. CUTOFF TEST FOR ELECTRIC WATER HEATERS AT HIGH TEMPERATURESThe electric water heater drawing (left), which illustrates the sequencing technique for electric water heater elements, is courtesy of Carson Dunlop Associates and is used with permission.
- Electric water heaters contain two heating elements – thick metal loops that become hot when electricity goes through them.
- A dip tube is used to supply cold water to the bottom of the tank when it is filled with hot water.
- When there is a significant demand for hot water, the higher heating element functions as a “booster” to provide more heat.
- As we said before, if there is some hot water available but it is restricted in quantity or temperature, it is possible that one of the heating components has failed and the other has not.
- However, while the bottom element is capable of heating the entire tank, it is not capable of heating the water to the same high temperature as if both elements were in operation at the same time.
- If the electric water heater continues to generate hot water at the same temperature as before, but the quantity produced appears to be significantly reduced, we think that the bottom water heater element has burned out.
- Cold water enters the water heater and collects at the bottom of the tank.
- A faulty bottom water heater element results in a short hot shower.
See HOW TO USE A DIGITAL MULTIMETER (DMM) for more information. For further information on how to safely use electrical test equipment, read SAFE USE OF DMMS AND VOMS and VOLTS / AMPS MEASUREMENT EQUIPMENT.
Steps in Testing an Electric Water Heater Heating Element – Good Method
When I switch on the hot water in the house, the water does not get hot – Claude 11/29/12
The components in your water heater could need to be replaced, Claude. See the following article for the steps to do the test:
- You should have done this earlier if you followed the steps above. Turn off the electricity to the water heater. Power should be turned off at the water heater circuit at the main electrical panel. Heater water should be lukewarm or cooler than the rest of the house. If the water heater is hot, run hot water throughout the building (without turning off the electrical power to the water heater) until the water is lukewarm or cooler. Removing the electrical wires from the heating element terminals is a good idea. (This is true whether the top or lower heating element is being tested.) To check for current flow, do the following: Use a voltage-ohmmeter, digital multimeter, or Ohmmeter or multimeter configured to read “resistance” or “ohms” in the following ways: Link one alligator clip or one probe of the VOM to each terminal on the water heater element, or use a VOM probe to connect them. One probe makes contact with one terminal, while the second probe makes contact with the other terminal. If the Ohmmeter needle does not move (or if no reading is displayed on the DMM), this indicates that the electric water heater heating element is faulty and must be repaired or replaced immediately. if the ohmmeter needle moves, or if you receive an Ohm value (other than infinity), then the heating element is in good working order, and you are ready to proceed to testing the other heating element on the heater. Briefly stated, if there is “continuity” through the heating element, it is functioning correctly. If there is no continuity (i.e., no electrical current can flow), the element is said to be faulty.
Testing an Electric Water Heating Element for a Short Circuit – Crude MethodOHM Table for Water Heater Elements
You should have done this earlier if you followed the steps above. Turn off the electrical power to the water heater. The water heater circuit should be turned off at the main electrical panel. Heater water should be lukewarm or cooler than the rest of your house. Assuming the water heater is hot, circulate hot water around the building (without turning off the electrical power to the water heater) until the water is lukewarm or cooler. The electrical cables should be disconnected at the terminals of the heating element.
Current flow is checked using the following procedure: The following is how to read “resistance” or “ohms” with a VOM, DMM, or Ohmmeter or multimeter: Each terminal on the water heater element should be connected with one alligator clip or one probe of the VOM.
If the Ohmmeter needle does not move (or if no reading is displayed on the DMM), this indicates that the electric water heater heating element is faulty and needs to be repaired or replaced immediately.
Briefly stated, if there is “continuity” through the heating element, it is functioning properly.
- Turn off the electrical power to the water heater—if you followed the directions above, you should have done this earlier. Power should be turned off at the water heater circuit at the main electrical panel. As previously mentioned, remove the access panel lid and insulation from the top or bottom water heater element (as applicable). Connect one of the heating element’s terminals to the alligator clip or test terminal of your continuity tester using an alligator clip or test terminal. You can see it right there on the heating element itself: a wire and a screw. A bolt or bracket that keeps the heating element in place should be connected to another probe of the continuity tester (also known as a VOM). A short circuit in the heating element will result in the test light turning on, the buzzer sounding, or your VOM (set to Ohms) indicating continuity
- The heating element will need to be replaced.
In addition, the Residential Gas and Electric Water Heater Handbookprovided by A.O. Smith and linked-to atREFERENCES has further water heater element testing guidelines.
Causes of Heating Element Failure on Electric Water Heaters
Water heater components can fail due to a variety of factors, including age and usage. If your building’s water source is hard water (rich in mineral content), scale buildup on the elements can hasten their mortality. For more information on how to remove scale from a water heater, see WATER HEATER NOISE DIAGNOSIS, CURE.
Reader Q A – also see the FAQs series linked-to below
John Are you checking the water heater element with:- all power to the heater turned off (so you don’t get electrocuted)and- all cables attached to the heating element removed from each other? If it doesn’t work, let’s try something else. If you continue to experience infinite resistance or zero resistance, it is likely that the heating element is blown out. When I try to use my multiple on ohms x 1k, it only works on the highest scale, and I’m reading continuity through the element. Was there a possibility that the components were being read via the water due of the high scale and by element was bad?
- Briefly stated, if there is “continuity” through the heating element, it is functioning correctly.
- Thank you for your inquiry.
- It should be replaced.
- When testing the terminal of an element and the body of the element, what is an acceptable resistance reading?
- It’s possible that we might begin by clarifying the question.
- When doing an insulation resistance test on a water heater circuit, there are two concerns to take into consideration.
- “Best grade thermo stant” is a phrase that I am not familiar with.
- Wishing you the best of luck on your test.
- Replace the element in your electric water heater by continuing to read.
Alternatively, choose a topic from the closely related articles listed below, or browse the entireARTICLE INDEX. For further information, visit the ELECTRIC WATER HEATER ELEMENT TEST FAQs- questions and answers originally provided on this page. Alternatively, consider the following:
- HOW TO USE A DMM DIGITAL MULTIMETER
- ELECTRIC WATER HEATER ELEMENT REPLACEMENT
- ELECTRIC WATER HEATER ELEMENT TESTS
- ELECTRIC WATER HEATER REPAIR GUIDE-HOME
- WATER HEATER NOISE DIAGNOSIS, CURE- remove scale from loud water heater
- ELECTRIC WATER
Suggested citation for this web page
ASSESSMENT OF THE ELECTRIC WATER HEATER ELEMENTatInspect An online encyclopedia of building environmental inspection, testing, diagnosis, repair, and issue preventive information is available at Apedia.com. Alternatively, have a look at this.
INDEX to RELATED ARTICLES:ARTICLE INDEX to WATER HEATERS
ASSESSMENT OF THE ELECTRIC WATER HEATER ELEMENTSATInspect An online encyclopedia of building and environmental inspection, testing, diagnosis, repair, and issue avoidance guidance is available at pedia.com/building. Alternatively, take a look at the following:
Ask a Question or Search InspectApedia
Comments or questions regarding how to test the heating elements on an electric water heater are welcome. We encourage you to use the search box just below, or if you prefer, you may make a question or remark in theCommentsbox below and we will get back to you as soon as possible. InspectApedia is a website that allows you to search for things. Please keep in mind that the publication of your remark below may be delayed if it contains an image, a web link, or text that seems to the program to be a web link.
We sincerely apologize for the inconvenience.
Citations can be shown or hidden by selecting Show or Hide Citations. InspectApedia.com is a publisher that provides references. Daniel Friedman is an American journalist and author.
How to test water heater element
Ohms is resistance Volts squared divided by watts = ohmsWatts and volts are printed on end of each element.240 volt water heater, 4500 watt elements: 57600 divided by 4500 = 12.8 ohmsHowever,there are a wide range of results and element can still be good.Applies to cold element, and not hot.Cold resistance: measuring ohms across both screw when no wires are attached to element and element is not heated.Hot water in tank raises resistance on element.Let element cool before doing ohm test so you are measuring cold resistance.
Advantage of non-contact voltage tester: ease and safety since wire nuts are not removed.Never assume power is OFF.Touch end of tester to each black, white, and red wire.
If tester flashes repeatedly like alarm, then voltage is present.
Remove wire nuts.
If tester light comes on with any test, electricity is present.See basic water heater circuit
You may need to cut back the foam to work on parts.
When finished, thermostats and elements must be covered by insulation again or thermostats become exposed to cool air and will misread tank temperature.Always best to put safety cover back into place when finished.
If water heater makes some hot water, then lower element is suspect.
Test both elements.If water heater is tripping circuit breaker, then test both elements and look for burned and melted wire.Resources:What to do if melted/burned wire is foundWater heater is tripping breakerTroubleshoot electric water heaterHow water heater worksHow to wire thermostatsTest electricity to water heater
test upper element
Lower wattage means slower heating and slightly less first hour delivery.Buy:Water heater elements Low density elementResourceCalculate first hour
For 30 gallon tank with 3500-Watt elements, reading is about 16 Ohms.
No reading means element is bad.Check watt and volt rating printed on each elementApplies to COLD element.
Test both screws.If multimeter reads any Ohms at all, or if needle moves even tiny bit, then element is shorted and needs replacementsee how