Do It Yourself Plumbing Made Easy: How to Install a Water Heater with NIBCO Flexible Push Connectors
It might be scary to think about installing a water heater yourself, but NIBCO Flexible Push connections provide a quick and simple solution that requires no solder, crimping, joining material, or special skills. Simply press the connecting tube into the valve, connection, or fitting until it comes to a complete stop. In addition to creating a secure connection, the removal tool makes it simple to disengage any joint, allowing for installation times that are up to 95 percent quicker than traditional joining methods.
To properly add NIBCO Flexible Push connections to your water heater, follow the steps outlined in this document.
Step 1: Getting Started
- Follow the manufacturer’s instructions for installing Flexible Push connections until you are ready to join the water line
- This will ensure that the connectors are properly installed. Keep in mind that the main water valve, gas supply, and/or electric supply should all be disconnected and turned off.
Step 2: Attach hose to nipple and mark tube
- Tie the threaded end of the Flexible Push connection to the water heater nipple (water heater nipples may or may not be provided with your water heater). Determine the location of the copper water line severed using the flexible hose
- Ensure that the tube is marked at least 2″ below the push fitting end of the copper tube.
Step 3: Cut tube
- Cutting copper tube water lines square with a tube cutter or fine-toothed saw after taking your measurements is a good idea. It is possible for water to leak out. Inside and out, use a half-round file or other deburring tool to remove sharp edges from the tube
- Clean the tube end to ensure that all debris, oil, and grease are removed from it. If you are utilizing PEX tubing, you will need to use a PEX stiffener
- Otherwise, you will need to use a steel stiffener.
Step 4: Insert tube
- Make a mark on the tube to indicate the correct tube insertion depth for your application. Install pipe to a depth of 7/8″ for 1/2″ nominal pipe and 1″ for 34″ nominal pipe.
- Using a twisting motion, attach the push fitting end of the Flexible Push connection to the clean, undamaged pipe at the other end of the connector. Make cautious not to straighten the Flexible Push Connector hose too much or it may kink.
Step 5: Wrapping Up
- Examine whether or not the tube and fitting are firmly attached by examining whether or not the depth mark fits the release collar. Carry out the same procedure with the second Flexible Push connection. That’s all there is to it
- Nothing more.
Congratulations on your decision to use NIBCO Flexible Pushconnectors to install your water heater! It is clear from the examples above that NIBCO’s Push-to-Connect fittings, valves, and connectors are extremely simple to use, allowing you to save time while also making installations straightforward. They are also backed by a 25-year warranty from a firm you can trust. Do you require further information? “The Essential Push-to-Connect Quick Reference Guide” is available for free download right now!
- It is possible to do it yourself. Fixing a Burst Pipe with Push-to-Connect Fittings from NIBCO Made Simple
- Do It Yourself Plumbing Instructions Plumbing Made Simple: How to Install a Water Heater Using NIBCO Flexible Push Connectors
- Do It Yourself Plumbing Project Plumbing Made Simple: A Step-by-Step Guide The following are the characteristics and advantages of NIBCO Push-to-Connect Fittings:
How to: Install a Hot Water Heater with SharkBite
In order for a home to be comfortable, water heaters are essential. They are, on the other hand, sometimes difficult to get since they are tucked away in cramped quarters or small closets. SharkBiteflexible water heater hosesallow professionals to simplify water heater installations since they provide the following features:
- Working in confined places
- Simple connections between water heaters and pre-existing pipes that do not line up
- The ability to attach the water heater to practically any type of pipe material is essential.
SharkBite hot water heater connectors have been authorized for use with electric or gas water heaters that have a flu vent installed.
Braided vs. Corrugated Water Heater Hoses
SharkBite provides both braided and corrugated flexible water heater hoses, as well as ball valves for use with or without a heater. On the supply side of the water heater, ball valves on the water heater hoses offer a shutoff. To determine if hard piping to your water heater is necessary, check with your local plumbing regulations. When rigid pipe is not an option, stainless steel corrugated connectors can be utilized as a substitute.
Installing a SharkBite Water Heater Hose
- First and foremost, determine the pipe material. Measure the distance between the hot and cold supply lines and the water heater in order to select the appropriate length connection
- Et cetera Make sure to cut the pipe as cleanly as straight as you possibly can. Check to see that the pipe is clear of scratches and other debris. If you’re working with copper pipe, be sure there are no sharp edges or burrs on the pipe. Once this is completed, use your SharkBiteDeburrGauge tool to measure and indicate the insertion depth on your pipe. Hand tighten the female connector onto the pipe nipple and then tighten with a quarter turn using a wrench, being careful not to overtighten the connector. Is it necessary for me to use thread tape? No. SharkBite water heater connections employ a gasket to seal onto the nipples of the water heater pipe, so thread tape is not necessary. To install the fitting, push it all the way to the mark you just created. Then repeat the process on the hot water exit side
- Finally, switch on your water and double-check the connections to your hot water heater. If you detect water dripping from the pipe nipple connection, use a wrench to tighten the connection even further.
Installing a hot water heater using SharkBite is a quick, efficient, and dependable process. The field-proven design of our hot water heater connectors is simple, secure, and adaptable enough to meet the needs of any installation project, no matter how complicated.
Ways on How to Install Flexible Water Heater Connectors
Ways to Install Flexible Water Heater Connectors (with Pictures)»Blog»Ways to Install Flexible Water Heater Connectors (with Pictures) 63Views Because the best tankless electric water heateris a significant financial commitment, it is essential to understand how to properly maintain it. Because of the expense, I was apprehensive about purchasing one for my own usage at first. Every time I took a bath, I’d use the same method as before: a kettle. When I made the decision to spend my money on a heater, the outcome was absolutely amazing.
After purchasing a heater, I look into ways to include extra components into the unit in the event that something has to be repaired or replaced.
Because I’m quite frugal when it comes to spending money, I make it a point to carry out all essential maintenance tasks whenever possible. Furthermore, I take pleasure in investigating and troubleshooting my heater.
Two Ways on How to Keep a Water Heater Long-Lasting
Before learning how to install flexible water heater connections, it’s important to understand two simple techniques to keep a water heater in good working order.
- Always turn on the heating or set the thermostat to “vacation” mode. When it comes to heaters, one of the misconceptions I had was that I could save money by turning them off during idle periods. I was saving centavos, but when I had to fix it, it ended up costing me more. It’s also difficult to switch it back on, which leads to even more difficulties down the road. It’s a good thing that my heater has a vacation mode since it makes it easier to reheat the water
- Clean and drain the heater’s tank on a regular basis. I cannot guarantee the cleanliness of the tank despite the fact that I have not placed anything in it. It is critical to remove the water from the container every six months in order to eliminate any undesired residues from the container. My heater’s effectiveness is always hampered by the inches of silt that accumulates. It’s one of the reasons I use a wet/dry vacuum to remove the debris from the valve in the first place.
Although these methods may seem insignificant, they are all beneficial when it comes to extending the life of a heater.
Things to Prepare for Flexible Connectors Installation
An example of a heater component that is easily changed is the flexible connection. Making certain that it is flexible enough to allow for free adjustment is critical. Additionally, it is critical to keep it in good working order in order to avoid any undesired water leaks. In order to complete my heater connection installation, the following items were required:
- Flexible connections, a wrench, a measuring tool, and thread-seal tape are all included.
When it comes to installing connections, the measurement equipment is quite important in addition to the connectors themselves. It is possible that incorrect measuring of connection lengths will result in reduced water flow. Furthermore, I needed a tool to tighten the nuts, and I also used thread-seal tape to keep the connections from coming loose.
Step-by-Step Ways on How to Install Flexible Connectors
Additionally, when it comes to connection installation, the measurement device plays an important role as well. The flow of water might be compromised if the connecting lengths are not measured correctly. I also required a tool to tighten the nuts, and I used thread-seal tape to keep the connections from coming loose while I worked on them.
- Disconnect the circuit breaker or gas supply. In order to ensure the safety of everyone, it is critical to switch off the electric heater’s breaker first. For the reason that I’m using a gas water heater, I shut off the natural gas supply. Afterwards, I lowered the temperature setting on the thermostat to its lowest level. After making the switch, I switched off the pilot light and measured the length of both the cold and hot water lines. Despite the fact that these connections are flexible, it is critical to understand what size is required. Depending on the heater, it is available in sizes ranging from 12 to 24 inches. At home, I always use 12 inches since it’s a good length for my heater
- Turn off the water supply and drain the tank completely. It is necessary to switch off the cold water supply before turning on the hot water faucet in order to drain the water that has accumulated inside the container. In order to remove any leftover pressure in the tank, I shut off and lifted the lever of the pressurization valve. I then loosened the bolts holding the tank and the heater supply lines together. With the use of an adjustable wrench, I was able to unscrew the bolts that held my heater’s pipes together and the connections. Having loosened the nuts, I was able to discard the old lines because they were no longer serviceable. Furthermore, reusing these previously used lines will simply add to the effort
- Wipe the threads and wrap the thread-seal tape around them. After releasing the nuts, I washed the threads of the male connections with a rag to clean them. These connectors are located on the tank’s roof and at the tank’s wall. After cleaning, I wrapped it with thread-seal tape, which I placed in two to three layers. Next, I prepared the new connections and connected them to the pipes from the tank. I then fitted the new connections and tightened them down with my wrench when the threads were completely finished. It is critical to restrict the flow of these lines in order to prevent unintended leaks. Furthermore, tightening them will save me from incurring further costs. Turn on both the hot water faucet and the water supply valve at the same time. For the purpose of determining whether or not I was successful in connecting the new connections to my water heater, I turn on the faucet and the supply valve. When the spigot started to provide me a steady stream of water, I kept it open. As soon as you’ve verified that the water is flowing continuously, you can turn off the faucet again. When it comes to electric heaters, just turn the breaker back on, while for gas heaters, there is an instruction supplied on the side. Even these electric warmers simply require the beaker to work, it is possible that they will be damaged if the faucet is still running. When it comes to gas water heaters, there are precise instructions on the side of the container, much like what I followed. The heater is now operational once the breaker has been turned off.
Circuit breakers and natural gas supplies should be turned off as well. In order to ensure the safety of everyone, it is critical to switch off the breaker for the electric heater first. I switched off the gas supply since I’m using a gas water heater. Afterwards, I lowered the thermostat’s temperature setting to the lowest possible level. Then I switched off the pilot light and measured the lengths of both the cold and hot water pipes. It is critical to understand the required size of these connections despite their flexibility.
- At home, I always use 12 inches because it’s a good length for my heater; turn off the water supply and drain the tank; repeat as necessary.
- In order to remove any leftover pressure in the tank, I shut off and lifted the lever of the pressurization valve.
- I used an adjustable wrench to release the bolts that link the pipes of my heater to the connections on the walls of my garage.
- Furthermore, reusing these previously used lines will just add to the difficulty; wipe the threads and wrap the thread-seal tape around the spools of threads.
- They are located on the tank’s roof and along the tank’s wall.
- Next, I prepared the new connections and connected them from the tank to the pipes.
- Keeping these connections restricted is critical in order to prevent undesired leaks.
- Turn on the hot water faucet as well as the water supply valve if applicable.
- When the spigot started to produce a steady stream of water, I left it open for a little longer.
- When it comes to electric heaters, just turn the breaker back on, while for gas heaters, there is an instruction on the side.
If you’re using a gas water heater, there are precise instructions on the container’s side, just like I did. The heater is now operational after the breaker has been reset.
How do you install a flexible water heater connector?
The following are simple procedures to follow while connecting connections to a heater:
- Disconnect the circuit breaker or gas supply
- Inspect the length of both the cold and hot waterlines
- And Shut down the water supply pipe and empty the tank of water. Remove the tank and heater supply lines from their mounting brackets. Using a thread seal tape, wrap the threads and secure the threads.
The use of CSST (corrugated stainless steel tubing) or flexible gas line pipe as a gas drop to the water heater is strictly prohibited. The bonding of your existing gas line will be necessary at this time if it contains CSST that has not been previously bonded. In addition to the foregoing, how can I conceal my water heater? Curtains. The most straightforward method of concealing your furnace and water heater is to use a sliding curtain as a barrier. You will need to measure the height of the wall in order to establish the appropriate curtain length, as well as the required curtain width.
In this regard, why is PEX prohibited in the state of California?
PEXpipe was first developed in California in 1990, according to Uponor Wirsbo, who claims that the product is effective in addressing difficulties in locations with aggressive soil conditions that copper pipe cannot address.
SharkBite fittings are built to last for a long time.
How to Change Water Heater Connector Hose
Water heater supply pipes can corrode and leak at the connecting nuts if they are not properly maintained. When this occurs, it is critical that the connecting lines be replaced immediately. Alternatively, you may purchase replacement hoses for your water heater online, or you can locate them at most hardware stores. Once you receive your new replacement lines, follow these seven steps to replace the hoses that link your water heater to the tank. The first step is to turn off the electricity to the water heater at the circuit breaker.
- Run both hot and cold water through the supply pipes from your kitchen sink faucet in order to drain them.
- Fourth, pull up on the pressure release valve on your water heater and keep it in place for a few seconds to let the pressure in your water heater’s inner tank to diminish.
- Step 6: Connect the new water heater connection hoses to the water heater.
- Connections: Connect the cold water line to the intake marked “Cold” or “C,” then connect the pipe to the cold water supply valve.
- Please keep in mind that while utilizing Hippohose Water Heater Connector Hoses, you just put our connection over the pipe to create a watertight seal in seconds.
- Step 7:Return the cold water supply and the breaker switch to their respective positions.
It’s as simple as pushing our Connection System over the current pipe and our specially designed stainless steel teeth will bite down and hold the pipe like a Hippo. The O-ring on the Hippohose will then compress, resulting in a watertight seal.
Water Heater Installation
Mr. Fix-It-Up-For-The-Family Water heaters that are beyond repair leak, waste energy, and can actually leave you in the cold. This article will teach you how to install a new gas or electric water heater on your own, saving you a significant amount of money in the process. Time A busy day of work Complexity IntermediateCost$101–250
Mr. Fix-It-Up-For-Us. Water heaters that are beyond repair leak, waste electricity, and can actually leave you in the dark and without hot water. If you follow the instructions in this article, you will be able to install a new gas or electric water heater yourself and save a significant amount of money. Time A full day’s worth of activities Complexity IntermediateCost$101–250
Time, materials and money
Mr. Fix-It-Up-For-Us Water heaters that are beyond repair leak, waste electricity, and can literally leave you freezing. This article will teach you how to install a new gas or electric water heater on your own and save a significant amount of money in the process. Time A long day’s work Complexity IntermediateCost$101–250
Water Heater Cost
A new water heater will range in price from $250 to $500, depending on the size, efficiency, and warranty included in the purchase. It is dependent on your situation and local codes which materials you will require for the installation.
Water Heater Installation Codes
Although you may have previously dealt with plumbing and gas lines, it is always best to be safe and call your local department of inspections. Obtain a permit (if one is necessary) and consult with an inspector about your installation intentions.
Turn off the gas and water
By twisting the handle a quarter turn, you can switch off the gas. When the handle is in the “off” position, it is perpendicular to the pipe.
Photo 2: First disconnect the gas
Disconnect the gas line at the “union” fitting and turn off the gas. Place the bigger wrench on the nut and a second wrench on the union’s collar to secure it in place. Set the wrenches a quarter turn apart at the beginning of the project.
Photo 3: Cut the cold water line
Unplug the gas supply from the “union” fitting. Holding the union’s collar in place with a larger wrench, tighten the nut down with the smaller one. Set the wrenches a quarter turn apart at the beginning of the process.
Update Your Gas Valves
If your valve does not look like this, check “Old gas valves can leak” for more information.
Disconnect the gas, vent and water lines
Disconnect the gas line at the union where it meets the water line (Photo 2). Then, disassemble the threaded “tee” and “drip leg,” and remove the nipple from the water heater gas control valve, following the directions on the package of parts. Avoid throwing them away since you will require them for the new water heater. The nut on a copper or flexible supply line may simply be unscrewed to access the gas line. Remove the sheet metal screws from the vent pipe in order to dismantle it. Wearing gloves is recommended since the metal piping’s edges are sharp.
- However, if you discover even the smallest of holes, splits, or rust, discard them in the garbage.
- After that, use a tubing cutter to cut the copper water lines (Photo 3).
- If you have galvanized steel pipes, you should detach unions in the same way that we did with the gas union in Figure 2.
- It’s possible that you’ll be able to utilize it on your new water heater.
Sediment may be obstructing the drain valve if the heater is not emptying as quickly as it should. Allow it to drain for as long as feasible, and then transfer the heater outdoors so that you may remove the drain valve from the tank’s drain valve assembly.
Reconnect the water
Reestablish the water supply. To begin, replace the existing valves so that you can turn on the water to the remainder of the home. Install nipples next, followed by threaded fittings and “stubs” of pipe to complete the installation. Hold the final component in place until the length is determined.
Photo 5: Make the final connection
Slip couplers are used to complete the final connections. Make certain that the coupler does not slip down when it is heated. Install the drain pan so that the entrance of the drain pan faces the floor drain. Hire a friend to assist you in lifting and setting the heater in the pan. If you’re changing the isolation valve, you’ll need to solder the new ball valve in place after that. Dielectric nipples should be screwed into the new water heater. These plastic-lined nipples help to minimize corrosion and extend the life of your water heater.
- Make careful to treat the threads with pipe thread sealant or cover them with Teflon tape before installing the pipe.
- Tighten the cooled fittings onto the nipples until they are snug.
- (Photo 5).
- For information about soldering copper pipe, type “solder” into the search box above.
- Use 3/4-in.
- If you are using galvanized tubing, you should cut off the threads at the bottom to prevent someone from capping off the blow tube in the case that the T P valve leaks.
Install the new vent
Sheet metal screws are used to attach the vent pipe to the hood. No matter how narrow the hood’s aperture is in comparison to the vent pipe, never employ a reducer. Attach the new draft hood to the water heater using sheet metal screws and secure it in place with the screws. Check your heater’s installation instructions for the suggested vent pipe diameter for your particular model. If the suggested vent pipe diameter is greater than the vent hood opening, there is no need to use a reducer in this situation.
Make sure that the pipe slopes down toward the water heater by 1/4 inch per foot of pipe length on any horizontal portions of venting.
Then proceed to attach the new vent pipe parts to the flue as you did previously. For each vent pipe junction, most plumbing rules require a minimum of three screws to be used. Sheet metal cutting tips may be found by searching “sheet metal” in the search box above.
Hook up the gas
Sheet metal screws are used to attach the vent pipe to the hood. No matter how narrow the hood’s aperture is in comparison to the vent pipe, you should never use a reducer to close the hood. With sheet metal screws, attach the new draft hood to the water heater and you’re done. Refer to your heater’s installation instructions to determine the required vent pipe diameter. Don’t install a reducer if the recommended vent pipe diameter is greater than the vent hood opening. Before you install the adjustable elbow, you must first measure a straight portion of new galvanized vent pipe that will climb as high as feasible (the higher the rise, the better the draft).
Small lengths of pipe should be bent out and screwed directly to the vent hood to prevent leaking (Photo 6).
Generally, a minimum of three screws are required for each vent pipe junction in accordance with plumbing rules.
Photo 8: Determine correct nipple length
To establish the right nipple length, take a measurement between the union and the tee and add one inch.
Photo 9: Test for leaks
Check for leaks by scrubbing each connection with soapy water. If you notice bubbles, you should tighten or reconnect the joint. Gas-rated pipe thread sealant or tape should be applied to the gas nipple (do not use normal white Teflon tape), and the pipe should be threaded into the new gas control valve. Using two pipe wrenches, tighten the nipple until it is snug (Photo 7). Assemble the tee and drip leg using the same two-wrench assembly method as the other legs. It may be necessary to measure for a new nipple if the original portion of pipe below the union is no longer suitable (Photo 8).
- Add 3/4 in.
- to this measurement and you’ll have enough money to buy a new nibple.
- You may purchase a leak detector in a handy spray bottle ($3), or you can make your own solution ($3) from scratch (one part dish detergent, two parts water).
- Continue to leave the faucet open until water starts to flow.
- Following the manufacturer’s directions, turn on the gas valve and ignite the pilot light on the stove.
- Instead of lighting a match or using a lighter to ignite the pilot, you simply press a button.
- Close all doors and windows, and put on the exhaust fans in the kitchen and bathroom.
- The smoke should be pulled up and out of the room through the vent.
- Turn off the gas and contact a licensed plumber for assistance.
Last but not least, adjust the thermostat to a comfortable setting. (For assistance, type “water heater temperature” into the search box above.) You’ll have enough hot water for a nice shower in around two hours, which will be well worth the wait.
Old Gas Valves Can Leak
The “grease-pack” valves that are commonly seen in older homes have a tendency to leak as they get older. Even though your local code does not demand replacement, we recommend that you install a ball-type gas valve ($10) in its place ($10 per valve). It is not difficult to replace the valve; you simply remove the old one and screw on the new one. However, you will need to turn off the main gas valve and then relight the pilot lights. If you don’t know how to complete these activities, you should hire a professional plumber, who will charge between $80 and $150.
Local Code Requirements
There are a variety of accessories available for your new water heater at your local home center. Some are needed by municipal regulations, while others are simply wonderful ideas. Plumbing codes differ from one jurisdiction to the next, so verify with your local inspector. Valve for turning off the gas All codes need the installation of a gas valve near the water heater. If you have a “grease-pack” valve, go to the section above titled “Old Gas Valves Can Leak.” Earthquake straps are another option.
- $12 for a pair of shoes.
- Gas line that is adaptable Flexible natural gas lines can tolerate movement and are frequently required in seismically active regions.
- Leg with a drip Before reaching the water heater’s control valve, any dust or grit in the gas line is collected in this small portion of pipe.
- Even though it is not needed by code, having a second valve on the hot line makes replacing the water heater in the future much easier.
However, you may want to utilize them simply because they are simple to set up.
Installing a drain pan, on the other hand, is a smart idea in any place.
Blow tube for $34.99.
Most of the time, a gap of 18 inches or less is necessary between the blow tube and the floor.
Water Heater Bonding
The installation of a bonding wire between the cold and hot pipes and the gas line is required by New Jersey building rules. Despite the fact that the majority of local codes do not need bonding wires, they are nonetheless useful. According to the experts we spoke with, bonding wires may actually help to increase the life of a water heater by channeling electrolysis away from the anode rod and tank—even on electric water heaters—and into the tank.
So, whether or not your local code requires the installation of a bonding wire, you may want to consider doing so to extend the life of your water heater. This small project is quite straightforward. It just costs approximately $10 and takes about 10 minutes to complete the process.
Required Tools for this Project
Make a list of all of the equipment you’ll need for this DIY project before you begin; you’ll save both time and frustration this way.
Required Materials for this Project
Preparing all of your stuff ahead of time can save you time and money on last-minute buying visits. Here’s a list of things to do.
How to Replace Water Heater Supply Lines
Your water heater is equipped with a cold water line that continuously supplies water to the water tank while you are using the hot water supply. The tank’s hot water is sent throughout your home via a second pipe, which is used for showers, baths, dishwashing, and laundry. If one of the water lines begins to show indications of corrosion or leaks, you should consider replacing one or both of them. You should make use of flexible water lines such as those included in water heater installation kits, particularly if you reside in an earthquake-prone location.
- While using hot water, your water heater includes a cold water connection that continuously feeds water into the water tank. The tank’s hot water is sent throughout your home via a second pipe, which is used for showers, baths, dishes, and laundry. If any of the water lines begins to exhibit indications of corrosion or begins to leak, you should consider replacing one or both of the water lines immediately. If you reside in an earthquake-prone location, you should use the flexible water lines included with water heater installation kits.
- Measure the length of the hot and cold water supply lines on both sides of the house. Since the length of these flexible copper lines can range from 12 to 24 inches, acquire lines that are the same length as your present water lines.
- Inspect the hot and cold water supply pipes to ensure they are both the same length. Since the length of these flexible copper lines can vary from 12 to 24 inches, acquire lines that are the same length as your existing water lines.
- Inspect the hot and cold water supply pipes to determine their lengths. Since the length of these flexible copper lines can range from 12 to 24 inches, acquire lines that are the same length as your existing water lines.
- Wipe the threads on the male connections on the wall and the top of the water tank with a rag to remove any dirt or debris from them. Wrap the threads in two or three layers of thread-seal tape to keep them from unraveling.
- The new lines should be connected to the pipes that are protruding from the wall. With the adjustable wrench, tighten the connections until they are snug. Using the opposite end of the wires, connect them to the connections on top of the water heater and tighten them down
- Restart the nearest hot water faucet by turning it on once again. Fill the tank with cold water by turning on the cold water supply valve. Maintain a continuous stream of water coming out of the faucet by leaving it turned on. Turn off the hot water faucet if it is on.
If you have an electric water heater, turn the breaker back on. If you haven’t already, turn off the hot water faucet before turning on the breaker to the water heater. If you switch on the breaker to the water heater before the tank is completely filled, the heating elements in the water heater will be damaged. Continue by following the stated instructions on the tank’s side to restart your gas water heater.
Things You Will Need
- Tape measure
- Adjustable wrench
- Thread-seal tape (optional).
How To Install Flexible Water Heater Connectors
tape measure; adjustable wrench; cloth; thread-seal tape (if desired);
Kinetic 1500Mm Flexible Water Connector.
The flexible water heater connections from Sharkbite make the installation of water heaters quick and simple. How to select the most appropriate water heater connection. Make a cut in the pipe, press it, and the shark grip seal will establish a tight seal without the need for an additional device.
Flexible Braided Stainless Steel Water Heater Connector.
Using Sharkbite’s flexible water heater connections, you can quickly and easily install new water heaters. Find out how to select the most appropriate water heater connection. Make a cut in the pipe, press it, and the shark grip seal will establish a tight seal without the use of an additional mechanism.
How To Replace A Water Heater Flex.
The length of both cold and hot water pipes should be measured. Gastite stainless steel braid flexible gas connection with a length of 1200mm. Install a shutdown valve on the cold water side of the water heater if there isn’t already one there before connecting the water heater.
Turn Of The Breaker Or Gas Supply.
Remove the tank and heater supply lines by loosening the bolts on the tank and heater supply lines. Make a mark on the tube to indicate the correct tube insertion depth for your application. All connections are available in a range of lengths to comply with cpvc and pex manufacturer installation instructions, as well as the ipc and upc model codes recommendations for electric and water systems, among other requirements.
After Getting The Right Length, Use The Wrench To Install One Of The Ends To The Flexible Gas Connector And Then Tighten Up The Channel Lock.
Remove the tank and heater supply lines from the tank by loosening the bolts on each. Create an insertion depth mark on your tube to show the correct tube insertion depth.
All connections are available in a range of lengths to comply with cpvc and pex manufacturer installation instructions, as well as the ipc and upc model codes recommendations for electric and water systems, among other things.
SharkBite U3088FLEX18BVLFA Flexible Water Heater Connector with Ball Valve, 3/4 Inch x 3/4 Inch FIP, Push-to-Connect Braided Stainless Steel, Water Heater Hose – Plumbing Hoses – Amazon.com
a rating of one out of five stars This product is not suitable for commercial sale. On November 29, 2016, a review was conducted in the United States. To begin, I must express my gratitude for the Sharkbite connections. They are truly remarkable. My experiences with them have been completely positive, and I believe their simplicity of use and high quality are revolutionary, allowing the typical person to feel more at ease and confident while tackling plumbing duties. The fact is that easier does not necessarily equate to better, and these hoses are a prime illustration of this; they are not suitable for commercial sale.
- I found some black particles in my bath tub.
- I purchased a brand new refrigerator less than 6 months ago, and around 3 weeks ago, it informed me that I needed to replace the filter, which I assume is due to the degeneration of these rubber hoses.
- I decided to go ahead and replace these hoses with copper ones.
- I immediately called a plumber to fix the problem.
- I’m not thrilled about having to spend money on repairing a faulty product; but, the thing that makes me nervous (or perhaps I’m just neurotic) is that my children, wife, and I have all been drinking this contaminated water.
- Sharkbite didn’t do a good job with quality control on this project.
- Hopefully, there will be no long-term harm to any of our equipment as a result of this product.
- Do not make a purchase.
Top reviews from the United States
verified purchaseReviewed in the United States on June 9, 2019Verified Purchase I’ve viewed a number of videos and it appears that chlorine in the municipal lines during the spring flush will eat away at the interior of these hoses. On June 14, 2020, a review was published in the United States of America. Overall, this is an excellent product. It was quite convenient not to have to purchase the fittings as well as the PEX tools to connect all of the connections. The service saved me both time and money.
- If you push whatever you are connecting too near to the fittings, you will get a kink in the line.
- This product is without a doubt recommended.
- It is quite simple to set up.
- It did spin a little, but there were no leaks after re-installing it!
- Highly recommended.
- These have left an impression on me.
- The only thing I was a little concerned about was the fact that it can kink if you had to maneuver it for an extended period of time before trying to tighten the end with the nut.
verified purchaseReviewed in the United States on May 10, 2017Verified Purchase Installing a new water heater has suddenly become a whole lot less complicated.
My water heater was replaced, and I installed a new whole-house water filter.
The valve and flex line assembly performed well in my experience.
Purchase that has been verified To me, the option to turn off the water right at the point of usage was essential.
I didn’t try to remove it because I didn’t have a reason to, but it appears to be a simple process.
Purchase that has been verified This device performs admirably and can be installed in seconds.
Having the cut off in place is a fantastic idea that may help you avoid filing an insurance claim.
If your water heater begins to leak around 3:00 A.M., however, this gem will come in handy immediately!
On October 7, 2021, a review was published in the United States of America. Once you have all of the shark bite equipment, the installation is straightforward. Cooper is far easier to use, but it is also significantly more expensive.
Top reviews from other countries
5.0 stars out of 5 for this product It is effective! On October 12, 2020, a review will be conducted in Canada. Purchase that has been verified My plumbing skills are limited to 2×4 construction at best, and I couldn’t find a plumber who would come to my house to install two cut-off valves on my water softener, so I took a chance on two of these products. I cut each copper line (both inflow and outflow), cleaned the ends, and held my breath as I put the valves with the Pex fitting onto the open ends of the copper pipes.
- There were no leaks and nothing occurred!
- There are no leaks.
- They are effective!
- The connections are substantial and sturdy, and they look to have been really well constructed.
- On May 1, 2021, a review was conducted in Canada, and a verified purchase was made.
- 5.0 stars out of 5 for this product Superoor Purchased on February 25, 2018 in Canada and reviewed on February 25, 2018
Water Heater Installation
When having a new water heater installed, be sure that the supply lines are made of robust copper. If at all possible, avoid using flexible copper or braided steel. Also, avoid utilizing shark bite fast connect fittings if at all possible. When used alongside water heaters, particularly on the hot water discharge line, these sorts of fittings are particularly susceptible to leaking. When upgrading a water heater, the majority of locations will require the installation or replacement of a thermal expansion tank.
A thermal expansion tank that has not been properly fitted or calibrated will not perform properly and may even fail prematurely if it is not maintained.
It is also possible that excessive water pressure will cause a tank to break prematurely. When it comes to replacing a water heater, the first step is to determine the current water pressure. A water pressure gauge, such as the one illustrated above, may be obtained for around $15. If the water pressure is excessive, a pressure relief valve (PRV) should be fitted to supply water to the entire home. As part of a water heater installation package, if the PRV is accessible, we will replace it for free.
Flexible Connectors vs Hard Pipe
We never use the flexible water heater connectors shown on the left since they are difficult to install.
These are time-saving connections that might break several years after they are first installed. Our company has replaced a number of water heaters that have flooded as a result of an improperly connected water heater flex connector. These water heaters have typically been in service for 7-10 years.
Get Rid of Saddle Valves
The saddle valve shown on the left is responsible for supplying water to the whole-house humidifier in the photo on the right. It is common for these valves to malfunction over time, and they are often positioned directly over the water heater. When working on the plumbing in the vicinity of or near these saddle valves, it is preferable to use full port, solid body, brass shutoffs rather than saddle valves. We will replace them at no further cost to you.
When it comes to installing a new water heater, one of the most important considerations is making certain that the gas appliance is correctly vented and is not leaking carbon monoxide into your house. Our technicians are experienced in replacing the whole flue for both your furnace and water heater, which is not unusual. On every project, we will have the components ready to go, and we will only charge for supplies if that is necessary. More information about water heater flue venting may be found here.