How to Light a Water Heater
Documentation Download Documentation Download Documentation You may see cold water flowing from your hot water faucet if you reside in a home that has a natural gas water heater. This is a good indication that your pilot light has gone out. It is not necessary to hire a professional in most circumstances; you will have hot water again in a matter of hours if the pilot is re-ignited correctly. While having your water heater’s instruction manual on hand is a good idea, it is not fully required because most gas water heaters need a similar process for relighting the pilot light, as described in this article.
- 1 Make that the pilot light is working properly. You will most likely need to remove a tiny panel at the bottom of the tank, known as an access panel, in order to determine whether or not the pilot light is truly turned off. If you do not see a little flame flickering, this indicates that your pilot light has failed.
- Depending on your water heater model, it is conceivable that your panel is not detachable and that you must observe your pilot light via a transparent window. It is possible that your pilot light has gone out if you are unable to see a flame burning through the glass in this situation.
- 2 Check to see whether there is any gas leaking. Never attempt to restart your pilot light if there is gas leaking from your water heater, as this is highly harmful to both you and your property. Instead, call 911 immediately. If there is any evidence of leaking, perform a basic smell test before trying to ignite the pilot again.
- Standing near to your water heater, sniff the air to see if you can notice any strange aromas. After that, get down on your knees and smell around any valves on the front and sides of the tank. Naturally, natural gas has no odor. To make it noticeable to humans, gas companies add an ingredient known as mercaptan to the mixture. When gas leaks, it has a sulfuric or rotten egg smell to it
- If you notice gas leaking in either of these locations (even in a faint scent), do not attempt to relight the pilot light. Remove yourself from the vicinity of the water heater and contact your gas provider immediately
- They will advise you on what to do next. Also keep an ear out for a hissing sound near the water heater, which might indicate a gas leak
- s3 Instructions may be found on the inside of the door panel of your water heater. Detailed instructions for your specific water heater model may be available here, and following them may assist you in the process of relighting the pilot for your unique water heater. Advertisement
- Step 1: Lower the temperature control setting to the lowest possible setting. 2Find the regulator valve, which is normally situated on the front of a box on the outside of the water heater
- 3Find the pressure relief valve. In most cases, this valve is positioned on the same box as the temperature control, but it is more likely to be on top of the box
- It regulates gas flow to the pilot burner beneath the hot water tank. To turn the knob off, turn it to the “Off” position. Wait 10 minutes after turning off the knob before proceeding to ensure that any remaining gas from the tank has cleared the air before continuing. The importance of safety cannot be overstated. 4 Determine the type of water heater that you have installed. Gas hot water heaters are often classified into two categories: “new” and “ancient.” Traditional heaters will require you to relight the pilot with your own flame, however newer design tanks are fitted with a pilot light igniter built in into the tank.
- However, while the specific appearance of the buttons on modern design tanks may vary, many of them include a red igniter button that is located a few inches away from the temperature and regulator valves.
- 5 Gather any lighting items that may be required. The pilot light on an old-style water heater must be re-lit with a “wand” lighter or fireplace matches since the pilot is too lengthy to reach with a standard lighter.
- Please avoid re-igniting a pilot using a standard lighted matchstick or miniature cigarette lighter, since doing so will force you to place your fingers in a small, tight position too near to the open flame, putting you at risk of being burnt
- 6Travel to the location of the pilot. The pilot is positioned at the end of the little silver tube that comes out of the control valve and is connected to the control valve. It’s possible that you’ll need to use a flashlight to see clearly in this location. Advertisement
- First, put the gas valve to the “Pilot” position by pressing down on it with your finger. Starting the flow of gas into the tube that provides the pilot light is accomplished in this manner.
- First, put the gas valve to the “Pilot” position by pressing down on it with your fingers. Starting the flow of gas into the tube that provides the pilot light is accomplished in this manner
- 2 Light the pilot burner with a match. The pilot gas valve or the red button will be held down with one hand while the other hand will be used to swiftly light the pilot.
- To use this button, make sure you have a new model water tank with a built-in ignition switch installed. You should be able to hear a clicking sound until the pilot burner comes on. If you have an old-fashioned heater, ignite the pilot burner with a wand lighter or match and wait a few minutes. Because you will be using one hand to push the valve/red button while using the other hand to ignite the pilot, you may require the assistance of another person to carry a flashlight for you if you require additional lighting. Make an effort to get assistance in advance so that you do not go halfway through a procedure only to be forced to halt because you are unable to see what you are doing
- To use this button, your water tank must be of the newer design with an ignition switch built in. Until the pilot burner ignites, you should hear a clicking sound. In the case of an old-fashioned heater, ignite the pilot burner using the end of a wand lighter or match. Given the fact that you will be using one hand to push the valve/red button and the other hand to ignite the pilot, you may require the assistance of another person to hold a flashlight for you if you require additional illumination. Make an effort to get assistance in advance so that you do not go halfway through a procedure only to be forced to halt because you are unable to see what you are doing.
Create a new question
- QuestionHow can I start a newer model gas heater that is on the market? Look up your model number and get in touch with the manufacturer for more detailed information. As a general rule, the most significant difference between a modern heater and these instructions is that newer types feature an electronic igniter (you simply press the button and a spark is produced) for lighting the pilot. Question What do I name the gadget that I use to ignite the pilot’s engine when I press a button on it? You refer to it as a “spark igniter.” Question What should I do if the pilot light on my water heater keeps flickering on and off? It is likely that you will have to replace it. Make contact with a supplier or even the firm that produced your water heater for further information. Question What should I do if the pilot light won’t remain lit for whatever reason? The most likely cause of your problem is that your thermocouple has to be repaired or replaced. A pilot light is a short copper tube that connects your water heater’s controls to the pilot light and has an end that sticks into the flame. Whenever the pilot light heats up the tip, it creates electricity that is detected by the control box, which allows it to determine that the pilot light is on. A new one is simple to install, and you can pick one up at any home improvement, plumbing supply, or hardware shop. Take your old one with you so that you may acquire the right measurement. A little bit longer is OK, but not typically much shorter
- Question When I press the pilot button, how long should I hold it down before pressing the little red ignitor button beneath it? It takes around 5 seconds. Restart it and make any necessary adjustments to the temperature. Question So, what should I do if the pilot light won’t turn on for whatever reason? Continue to try while keeping an eye out for any signs that there is gas coming through (usually by smell). The likelihood is that the regulator is faulty and that it will need to be replaced. This is also something that you can accomplish on your own.
Inquire about something There are 200 characters remaining. Include your email address so that you may be notified when this question has been resolved. SubmitAdvertisement
- If this procedure does not provide results, check to see that the pilot light’s base is not filthy or blocked. If it is, clean it well and repeat the process after 10-15 minutes. You may also try holding the valve/control button for an additional 30-45 seconds after the pilot light has been ignited. If this technique does not work, it might be due to a lack of gas pressure or a defective gas valve. If you are unable to light the water heater after many efforts, contact an appliance repair person, a plumber, or your gas provider. You may have a faulty thermocouple if the pilot light does not come back on after being re-lit or if it goes out soon after being re-lit. It is possible to see the thermocouple in the pilot light flame region because it extends from the temperature control into the flame area. The cost of one is pretty low, and you can do it yourself.
Thank you for submitting a suggestion for consideration! Advertisement
- If you detect the scent of gas anywhere in your home, contact your gas provider right once. Even a “little quantity of gas” is too much
- Do not re-open the gas valve until you have completed the replacement of the access panels and doors. It is possible that a flame will come out of the water heater if this is done.
Call your gas provider as soon as you notice any gas odors in your home or business. The presence of even a “little quantity of gas” is dangerous; do not re-open the gas valve until you have replaced all of the door panels. An explosion of flames from the water heater might result if you do so.
About This Article
Summary of the Article Set the temperature control to the lowest setting and turn the gas regulator valve to the “Off” position to begin lighting an electric water heater. X Then, by adjusting the gas valve to the “Pilot” position and pressing down on it, you may begin to pump gas into the system. After that, press the red ignitor button, which is located near the gas valve, to ignite the pilot burner. Hold down the pilot button for 1 minute longer than you think it should be and check to see whether the pilot is lit.
Continue reading for helpful hints on how to prepare for and light your water heater.
The writers of this page have together authored a page that has been read 388,843 times.
Did this article help you?
Prev PostNext PostWhen the pilot light on a water heater goes out, it is typically because of a natural fluctuation in gas pressure, which extinguished the flame. The most obvious indicator that a pilot light has gone out is the one that everyone dreads: the water will not heat up properly. In the event of a damaged flame sensor, it’s critical to know how to relight the pilot light on your water heater so you can get the flame going as quickly as possible. This will not only allow you to get your hot showers back, but it will also ensure that no gas is unintentionally discharged into the home.
However, for the vast majority of gas-powered water heaters, you should begin by locating the gas shut-off valve on the water heater, which is generally plainly labeled on the front lower section of the water heater, before proceeding.
Turn the knob to the “Off” position and wait five minutes for the gas to clear before proceeding with the next steps:
- Open the door or cover that provides access to the pilot light. In most cases, this will be positioned under the gas valve
- However, some water heaters will just have an open gap where you can see the pilot light burner instead. Locate the burner within the container using a flashlight or a headlamp. It will be reached by two little gas tubes. You’ll want to keep an eye on it while you’re at work. Turn the gas knob to the “Pilot” position and push and hold the button. This will initiate the flow of gas, allowing you to ignite the flame. Some water heaters feature a separate pilot mode button, which is commonly a red button, which you must push and hold in order to activate it. While keeping the gas pedal depressed, ignite the pilot light. Certain water heaters feature an igniting button that is red or black, while others must be lighted manually with a long lighter
- Some models include a red or black igniting button. Maintaining pressure on the gas knob or button for a full minute after the flame is ignited is critical. Then slowly release it while checking to see if the light is still on. Turn the gas knob to the “On” position and listen for the unmistakable “whump” or whooshing sounds that indicates the main burner has ignited. Enjoy your hot shower when you’ve replaced the lid.
Despite the fact that a single extinguished pilot light is normally caused by a natural fluctuation in gas pressure, recurrent faults suggest a more serious problem with the water heater itself. The most typical problem that causes repeated pilot outages is a filthy or bent thermocouple, which is a thin copper wire and rod that detects the presence of a flame and immediately switches the gas off when it detects a lack of flame detection.
What is a Thermocouple?
A thermocouple is sometimes referred to as a flame sensor in contemporary water heaters because of the way it detects flames. Your thermocouple is most likely twisted, filthy, or damaged if the pilot light continues to go out after you have completed the above-mentioned lighting procedures. For those who find that their pilot light is twisted and not near the burner, they may simply turn off the gas, shift it over, and attempt lighting the pilot again. It may be necessary to clean the water heater gas valve and the main gas line near the heater if this does not solve the problem.
- The burner is typically simple to remove by simply sliding it out.
- If this doesn’t solve the problem, you may get a new thermocouple for less than $15 at any hardware store or home improvement center.
- Rooter Plumbing to help you get hot water back into your home again.
- The use of hot water is simply one component of a great showering experience.
- Previous PostNext Post Previous Post
Why Your Water Heater’s Pilot Light Keeps Going Out & How to Fix It
The date is May 13, 2021. When the pilot light flame on your gas water heater goes out, it is an annoying and frustrating situation to have to deal with. When your water heater’s pilot light fails to stay lit, you’re left without hot water, which makes even the most basic of tasks such as taking a shower a chore. Naturally, you question, “How did this happen? What happened?” Is there anything you can recommend to help you get things going again? What should I do to have it repaired? “May you tell me about the costs I can expect?” Fortunately, if your water heater pilot light goes out, you should be aware that this is a frequent problem that many homeowners have and that the time and effort required to repair it is low.
Please allow us to guide you through some of the most frequent reasons why your water heater isn’t heating and how to resolve this issue if your water heater pilot light won’t stay lit and you are unfamiliar with water heaters.
Why does the pilot light on my water heater keep going out?
Because of problems with the heater’s thermocouple or owing to access to combustible air, your water heater’s pilot light continues going out repeatedly.
When your pilot light is on, your thermocouple detects the presence of the flame. The thermocouple’s tip is positioned above the pilot flame, providing a voltage that maintains the gas valve open in the process. A thermocouple will shut down the gas supply to your water heater if it detects that the pilot light on your water heater is not lighting up properly. When thermocouples are exposed to moisture or dust for an extended period of time, they might malfunction, gather dust, or get bent away from the pilot light’s flame.
Lack of Combustible Air
Another reason why your gas water heaterpilot light won’t remain lighted might be that there isn’t enough combustible air in the room where it is located. To keep the pilot light on in your water heater, you’ll need to blow air into it. Otherwise, the flame will be extinguished. Take precautionary measures to ensure that the water heater is not surrounded by material, such as litter or lint, which might increase the quantity of combustible air present. Maintain as much cleanliness as possible in the surrounding region.
What do I do if my water heater pilot light keeps going out?
The lack of sufficient combustible air in your gas water heater might be another reason for the pilot light on your gas water heater not to stay lit permanently. To keep the pilot light on in your water heater, you’ll need to blow on it. The flame will be extinguished if this happens. Make certain that the water heater is not surrounded by clutter, lint, or debris, since this will increase the quantity of combustible air in the vicinity. Maintain as much cleanliness as possible in the immediate vicinity.
- Locate the gas shut-off knob and turn it all the way to the “Off” position. The gas flow is halted as a result of this. Allow for a few minutes for the gas to dissipate before continuing. To get access to the burner, remove the access panel. To begin the flow of gas, turn the knob to the “Pilot” position. You’ll want to press and hold the knob down for a few seconds. While still holding the gas knob, ignite the pilot with a long lighter while still holding the gas knob. To ignite your gas water heater, use the button on the side of the tank that says “ignite.” As soon as the flames have been extinguished, turn the gas knob to the “On” position and wait for the main burner to come on.
If you are unable to relight the pilot or if your pilot light keeps going out, it is possible that you have another problem, such as a faulty thermocouple, to consider. Please refer to the owner’s handbook for your water heater equipment for further information.
Can I replace a thermocouple myself?
Yes. In the event that you are handy with tools, you may be able to change the thermocouple yourself. It is easier to accomplish this by turning off the gas valve and removing the entire burner and thermocouple assembly. In the case of minor repairs, it is preferable and safer to hire someone who is knowledgeable in the field of repair. A specialist may also evaluate your water heater for other faults and provide advise or ideas on how to deal with any existing or future difficulties that may arise.
Call BGE HOME
Please contact BGE HOME at (410) 918-5600 if your water heater pilot light will not light or continues going out. You may also contact us online. Our licensed specialists are available 24 hours a day, seven days a week to come out and inspect your water heater and make recommendations on how to get it running safely and effectively again.
This item was posted on Thursday, May 13th, 2021 at 4:09 pm and is filed under Uncategorized. Commenting and pinging are temporarily closed for this post.
How to Light the Pilot for a Gas Hot Water Heater
When the water in the tank needs to be heated, tank-type gas water heaters utilize a pilot light to ignite the gas burner, which then heats the water. The cold water flowing from the hot water tap is usually the first sign that your pilot light has gone out, so keep an eye out for it. Even if the equipment is not malfunctioning, a pilot light might go out for a variety of causes, including sudden swings in gas main pressure. If the pilot light on your heater goes out, you may relight it by yourself.
- Find the gas regulator valve on the water heater and turn it on. It is positioned on the exterior of the water heater, near where the gas line enters the device, and it is controlled by a knob on the outside. The gas supply to the pilot burner beneath the hot water tank is controlled by this valve. To turn the valve off, turn the knob all the way to the left. Wait five minutes before continuing. Locate the pilot burner, which is located beneath the natural gas water heater. Remove or unsnap any access cover that is preventing you from getting to the burner. Make use of the flashlight to illuminate the pilot burner
- Turn the knob on the gas regulator valve to “Pilot,” press down on it, and keep it pressed down. The flow of gas to the pilot burner is initiated by pressing this button. To start the pilot burner gas flow on some water heater types, you must push and hold down a separate red button for a period of time. Find a red or black button labeled “Ignition” on the top or side of the gas valve if your heater has a piezoelectric spark pilot igniter built in. To start the pilot, press the button on the control panel. As the igniter ignites, you will hear a click sound. If you must manually ignite your heater, a long-necked barbeque lighter is the most secure type of lighter to use. Light the pilot burner with a lighter flame and turn it on.
After the pilot has been ignited, keep the regulator valve knob firmly depressed for at least one minute. This permits the pilot flame to heat the thermocouple safety sensor, which detects the presence of a live pilot flame, allowing the pilot flame to heat the sensor. Reduce the pressure on the regulator valve knob gradually. When the pilot light continues to glow after you have released the knob, turn the knob to the “On” position. During the ignition of the primary burner, you should hear a muffled “whoomp” sound.
Things You Will Need
Look for a label on your gas water heater that provides particular pilot lighting instructions for the model of water heater you have installed.
- If you smell gas in the vicinity, it is not a good idea to attempt to relight a water heater pilot light (or to do any other maintenance on the device). When you are outside the home, dial 9-1-1.
Light Your Hot Water Heater Pilot Light in 5 Easy Steps
Posted at 12:00hinPlumbing Services on February 12, 2019 There are a variety of reasons why your hot water heater’s pilot light may go out. However, while the absence of a pilot light may signal a problem with the heater itself, a hot water heater pilot light can also go out for a variety of other causes, such as oscillations in the gas pressure. If your pilot light is out, you will most likely see cold water flowing out of your hot water valves when you turn on the water. The good news is that you can easily re-ignite your hot water heater pilot light by following these five simple steps:
1. Turn Off the Gas
The first thing you should do is make certain that the gas has been turned off completely. Locate the gas regulator valve in order to accomplish this. On the outside of your water heater, around the point where the main gas line enters the heater, you’ll often find this valve. Allow at least five minutes to pass after turning this valve to the “off” position to allow any leftover gas to disperse.
2. Where is The Pilot Light on Hot Water Heater?
This section will most likely necessitate the use of a flashlight. Most of the time, the pilot light for your hot water heater may be found beneath the water tank on your device. It is possible that you may need to remove an access panel in order to get to it. Some newer versions may have the pilot light hidden behind a glass panel, which is a nice touch. In appearance, the pilot light’s housing should be in the shape of a little silver tube. You will need to hire a plumber to diagnose any additional issues you may be experiencing with your water heater if there is already a flame burning at the end of this tube when the pilot light is turned on.
3. Check for any Gas Leaks
Ensure that there are no gas leaks or residual gas before proceeding any further. Igniting a flame in the vicinity of a gas leak can be extremely hazardous to your health and the safety of your property. Relighting your hot water heater pilot light should only be done if you are certain that no gas is leaking from the device. You may confirm this by doing a basic smell test as follows: Take a few deep breaths while standing near to your water heater and smelling the air. Despite the fact that natural gas is odorless, gas companies use an additive called mercaptan to guarantee that it may be discovered in the event of a leak.
If you don’t detect any rotten eggs-like odors in the air surrounding your water heater, step closer and sniff any of the valves, pipes, or connection points in the vicinity of the unit.
Immediately leave the house if you detect even a faint whiff of gas and contact your plumber, who will be able to advise you on what steps to do next.
When you leave the house, avoid turning on or off any lights since this might cause sparks that could ignite the gas.
Always leave the house before phoning someone or sending a text message. Natural gas that is leaking can make you sick, and spending any further time near a gas leak increases your chances of accidently inhaling or igniting the leaking gas.
4. Ignite your Hot Water Heater Pilot Light
It is safe to restart your hot water heater pilot light once you have determined that there are no leaks in your water heater equipment. To accomplish this, set the regulator valve to “pilot” and press and hold it down for a few seconds. Depending on the model, you may be required to press a second red button to regulate the flow of gas to the pilot light. If your machine includes a dedicated pilot button, it will most likely be red and labeled “pilot.” Check the front of your unit for instructions that may assist you in locating all of the valves and buttons necessary to re-ignite your hot water heater’s pilot light, if there are any.
When it comes to newer models, the “ignition” button on your water heater should be either black or red in color.
As this occurs, you should hear a clicking sound.
The safest method for accomplishing this is to use a long-nosed lighter, such as those used to ignite barbecue grills.
5. Make Sure the Flame Stays Lit, and Your Heater is Working.
Maintain pressure on the regulator valve for at least a minute after the pilot light has been ignited. The thermocouple sensor will be able to re-heat as a result of this. This sensor detects whether your water heater’s pilot light has gone out and will shut it down if the water becomes too cold to handle. Allow for a minute before carefully releasing the regulator valve and checking to see whether the pilot light continues to burn. If this is the case, switch the regulator valve to the “on” position.
Once this is accomplished, your pilot light should be operational.
Dealing with natural gas may be a frightening experience. It is possible, however, to safely rekindle your hot water heater pilot light whenever you need to if you follow these simple instructions. It’s always possible to call Benjamin Franklin Plumbing for skilled, timely, and locally-based assistance if you are still unclear of what you are doing, cannot figure out how your specific model works, or simply prefer to have a professional handle the situation instead. BFP Duncanville provides plumbing services to the Southwest Dallas communities of Cedar Hill, Dallas, DeSoto,Duncanville, Glenn Heights, Grand Prairie, Maypearl and Midlothian as well as the towns of Oak Cliff and Ovilla.
In addition to emergency plumbing repair, the company offers a variety of other plumbing services, including faucet repair, drain services, toilet repair, plumbing fixture installations, tub and shower installations, kitchen sink repair, faucet installation, water heater repair/replacement, and garbage disposal replacement, among other things.
For further information or to make an appointment, please contact us at (972) 263-5010.
How to Light a Water Heater’s Pilot Light (With Pictures)
With 23 years of experience in the HVAC sector, Dan has gained knowledge in a variety of areas, including installation, service, sales, and distribution. Some individuals may think that lighting the pilot on a hot water tank is an easy chore, but as a home service provider for over 15 years, I can assure you that I’ve made more than a few dollars executing this task for others. Despite the fact that many modern gas-burning appliances have converted over to hot surface or electronic ignition, there are still a significant number of standing pilot systems being made and used today.
It will be explained in detail in the following stages how to light your pilot, what to watch for when doing so, and a few other techniques you may use to get the fire started.
- 15 years of experience in HVAC installation and service
- 5 years of experience as a home improvement contractor
- Product safety, performance, and certification testing experience spanning more than two years
- EPAOSHA certification. Electrical theory, thermodynamics, and refrigeration coursework have been completed
This is an illustration of what a sealed combustion chamber on this sort of device may look like. It’s your looking glass, which is represented by this small square on the panel. Take note of the differences between this sort of control module and the earlier tank-style control module. In addition to being a control, the little knob on top serves as a button. View from above in order to notice the electrical spark button to the left.
Lighting a Sealed Combustion Pilot
We’ll start with a hot water tank system that is more contemporary and uses sealed combustion technology. With a sealed combustion chamber, there is no need to enter the burner assembly, and you should avoid doing so if at all possible. There is a looking glass in the access panel that you may use to visually verify if the pilot is lit. Everything you need to light this pilot is mounted directly to the burner control module. This access is bolted shut for a purpose, and it should only be accessible by individuals who are properly trained and licensed.
- Set the gas control knob on the top of the stove to the “pilot” position. To enable gas to flow, press and hold down the control knob itself for many seconds. Press and hold the electronic spark button, which is placed on or attached to your control module, until you hear it click. If there is a little amount of air in the line and it takes a few seconds to “bleed out,” you may need to click it a few times before the pilot is lighted. Continue to hold down the knob until the pilot has heated the thermocouple enough for it to be able to confirm ignition with the thermostat in the control module by visual confirmation. If the thermocouple does not heat up sufficiently, the pilot will be forced to return to the aircraft. Remove your finger from the control knob and visually check that the pilot is still glowing. To turn on the gas, turn the gas control knob to the “on” position. If the pilot was left out long enough for the water temperature to decrease, the burners should begin to operate within seconds of the pilot being turned off. If the water has not cooled, it is possible that there will be no need for the burners to be turned on. Be prepared for it to not start up immediately
- This is normal.
You are in the correct position if the notch is aligned with the button and the “pilot” is aligned with the indicator. The following is an illustration of what an open combustion burner assembly can look like. I’ve taken the two panels off so you can see what they look like on the inside. It is the copper line you can see in this shot that connects to the thermocouple, and the aluminum tubing that connects to the orifice where you will insert your lighter. Inside the room, the two come face to face.
Lighting an Open Combustion Pilot
Unlike the sealed combustion tank, you will be required to provide your own flame to light the pilot, rather than relying on an electronic ignition to do so for you. This process is very similar to the sealed combustion tank, with the exception that you will be required to provide your own flame to light the pilot yourself.
- The gas control knob should be set to pilot mode so that the notch in the dial corresponds to the button that controls the gas supply. If you do this, you’ll be able to press the button all the way down when it’s necessary
- Remove the panels from the burner compartments. Both should be quite simple to remove by raising up and pulling out. Place your preferred flame source (lighter, match, or other similar item) into the chamber such that the flame is directly beneath the aperture of the pilot supply line and ignite the flame. NOTE: I prefer to do three and then four. Despite the fact that the two stages can be exchanged, I believe it is better to introduce the flame before providing gas in order to minimize even the slightest possibility of gas buildup. I prefer to err on the side of caution, so I press and hold down the pilot gas supply button for many seconds before visually confirming that the pilot has been ignited. Keep the pilot gas supply button depressed for about 30-45 seconds to heat the thermocouple if this is the case. Release the button and visually check that the pilot light has not been extinguished. Assuming the pilot light remained on, turn the gas control knob to the “on” position.
Again, depending on your conditions, the water heater’s burners may or may not turn on straight immediately, so be patient.
Things You Can Use to Light a Pilot Light
- A long, thin candle
- A long, thin lighter
- Long, thin matches
- Short matches with a Hemostatic Clamp
- A long, thin candle
Don’t Have a Lighter or Matches?
Lighting a long, thin candle on the stove and utilizing it to light the pilot light may be an option.
When doing this, place a piece of tin foil behind the pilot to prevent wax from spilling onto the bottom of the chamber.
A Quick Water Heater Inspection You Can Do
- Lighting a long, thin candle on the stove and using it to light the pilot light could be a good idea. In order to prevent wax from spilling into the bottom of the chamber, place tin foil beneath the pilot when doing this procedure.
To the best of the author’s knowledge, the information in this article is accurate and complete. Content is provided solely for informative and entertainment reasons and should not be relied upon as a substitute for personal counsel or professional guidance in commercial, financial, legal, or technical problems, unless otherwise specified. Dan Reed was born in the year 2012. Dan Reed (author) wrote the following on April 22, 2012: Thank you so much, Mmargie. People who have never done it before may be nervous, but I always spend a significant amount of time thinking about my directions and selecting themes that are safe for anybody to try if the instructions are followed.
I’ve always been apprehensive about using gas appliances.
lolI feel a little better after reading the particular instructions on your site, despite the fact that I do not currently have any gas appliances.
How to Relight Your Water Heater’s Pilot Light
An Overview of How to Turn on a Water Heater Pilot Light
- Step 1: Turn off the gas
- Step 2: Put the controls in “pilot mode.” Step 3: Press the control button and the light button simultaneously. Step 4: Bring the water temperature back to normal. Step 5: Reinstall the lid.
Don’t freak out if you find yourself without hot water for no apparent reason. It’s possible that the pilot light on your gas water heater has gone out. Despite the fact that this little blue flame should always be burning, it can go out for a variety of reasons. The good news is that, in the majority of situations, relighting is a simple process. This Might Also Be of Interest to You: Using These 5 Simple Steps, You Can Relight Your Furnace Pilot Light Please see the following steps for relighting the pilot light on your gas water heater.
How Do I Know If My Pilot Light Is Out?
In the event that you turn on a faucet and the water comes out cold, no matter how long you let it run, it is likely that your pilot light is out. You’ll need to get to the water heater in order to examine it. Most water heaters have a pilot light that is situated at the bottom of the machine, below the gas control valve, which makes it easy to find. Look into the burner chamber by opening the access panel or entrance to the chamber. The pilot light tube may be found in this location, and it should have a continuous blue flame.
Can I Relight the Pilot Light by Myself?
In many circumstances, you will be able to relight the pilot light on your water heater by yourself. First, check sure there isn’t a gas leak in the area where you’re trying to relight the pilot light. Usually, a simple whiff will suffice to do this. Natural gas is usually scented by the utility companies in order to make it easier to discover leaks in your house. Most of the time, the scent is comparable to that of garlic or rotten eggs. If you suspect that you are smelling gas, do not attempt to relight the pilot light.
For further information, contact your natural gas utility.
Gas hissing and blowing noises may also signal the presence of a gas leak. As long as none of these warning indications are present, you should be safe in your attempt to relight your pilot light by yourself. Additional Related Articles:
- Here is an estimate of how much it will cost to replace a water heater: When your water heater isn’t working, you’ll notice these seven tell-tale signs. Learn how to properly drain a water heater. What is a Smart Water Heater and how does it work? I’m wondering how much a tankless water heater will set you back.
What Do You Do When the Pilot Light Goes Out?
Re-lighting the pilot light according to the manufacturer’s instructions for your equipment should be attempted if at all possible. The procedure, on the other hand, is very consistent across different kinds of gas water heaters. To begin, establish if your water heater is equipped with an automated or manual ignition system. A glimpse at the control dial should be enough to notify you, according to Mullen Plumbing, Heating, and Cooling of West Virginia. If you have an automated igniter, it is likely that you have an ignition button.
It will be necessary to manually relight your pilot light.
How to Light a Pilot Light on a Water Heater Without an Automatic Igniter
- Using the access cover, switch the gas control valve to the “off” position to cut off the gas supply. Allow about 10 minutes for any gas that has gathered to disperse. The “pilot” position is reached by turning both the control and the water temperature knobs. To activate the control knob, depress it. To re-ignite the pilot light, hold the button down while using a wand lighter or long match to ignite it. A continuous flame should be visible once the pilot light has been turned on. For a full minute, continue to keep the knob down to force air out of the line that has accumulated over the course of time. Turn the knob to the left
- Set the temperature of your water heater back to the appropriate level by turning the control knob. Remove the access cover and replace it.
How to Light a Pilot Light on a Water Heater With an Automatic Igniter
- Remove the access cover from the door. To turn off the gas, turn the gas control valve to its “off” position. Wait about 10 minutes for the gas to disperse before continuing. Then, set the control and water temperature knobs to the “pilot mode.” To use the control button, press it. While maintaining pressure on the trigger, continually push the striker knob for approximately 90 seconds, or until the pilot is lighted. The striker knob is usually either black or red in color. Continue to hold down the control knob for a full minute to bleed air from the line, then release it.
- Set the temperature of your water heater by turning the control knob to the appropriate setting
- Replace the access cover in a safe manner.
Your pilot light should remain bright if it was accidentally turned off due to a draft or similar one-time problem. If it doesn’t work the first time, wait 10 minutes before attempting to ignite it yourself again after that. Having trouble with your water heater’s pilot light? It’s possible that your device requires expert maintenance or repair. Because we are spending more time at home than ever before, it is critical to be prepared for unexpected home repairs with a plan from HomeServe. The knowledge that you can easily call our 24-hour repair hotline in the event of a covered breakdown provides you more peace of mind.
How To Relight the Pilot Light in Your Gas Hot Water Heater
When the hotwater heater in your home fails, duties such as showering, doing laundry, cleaning dishes, and other household chores come to a grinding halt. If you have a gas-powered hot water heater, it is possible that the pilot light has gone out, which is the root cause of the problem. In most circumstances, if you relight the pilot, you should be able to go back into the air again. In this post, we’ll demonstrate how simple it is to complete the task yourself.
What does the pilot light do?
The pilot light of your gas hot water heater is a tiny, continuously burning flame that serves to start the burner of the appliance. To put it another way, if the pilot light goes out, the unit will be unable to heat water. It is possible for a pilot light to be extinguished for a variety of causes, including something as simple as a short stoppage in the gas line or an air bubble in the gas line. Warning: If you smell gas at any stage throughout the process, leave the area immediately and contact your energy supplier as soon as possible.
Steps to relight the pilot light.
- Remove your foot from the gas pedal. Find the gas shut-off valve on your hot water heater and turn it off. The knob should be labeled in a clear and understandable manner. Turn the switch to the “Off” position and wait 5-10 minutes to ensure that all of the gas has been expelled. Locate the pilot light access point. Most of the time, this will be under the gas valve. To locate the burner and two gas tubes, open the pilot cover (if one is present) and use a flashlight to peer inside the hole to locate the burner and two gas tubes
- Return to the gas valve and turn the knob to the “Pilot” position. By depressing the knob all the way down, you will begin to feed gas to the pilot. There are certain hot water heaters that include a separate pilot button
- If this is the case, press that instead. While maintaining control of the knob or button, reach into the access and ignite the pilot with an extended lighter while still keeping it down. Once the pilot light comes on, keep the knob/button down for about one minute. Release the knob/button carefully after that period of time, and make sure that there is still a flame emanating from the pilot. Return to the gas valve and turn the knob to the “On” position. Typically, a noise will be heard to indicate that the primary burner is lighting
- After giving the heater enough time to restart, replace the access cover and inspect the hot water supply.
What happens if the pilot light goes out again?
The fact that the pilot won’t light or that it keeps going out is a clue that you may be experiencing another problem with your hot water heating system. The most typical issue we encounter is a thermocouple that is twisted, fractured, or filthy (also called a flame sensor). Because the typical service life of a hot water heater is 12-15 years, it may be a wiser investment in some situations to replace the unit rather than spend money fixing your existing unit.
if your water heater isn’t producing enough heat, call Reidelt Plumbing Inc. at (219) 322-4906 for assistance. Our professional plumbers will come out to your home, assess the situation, and provide recommendations on how to restore hot water flow in your home.
- This entry was published on April 30, 2020, under the category Water Heaters.
Solved! What to Do When Your Pilot Light Goes Out
Image courtesy of fotosearch.com The temperature in my shower this morning was absolutely freezing, and I mean that in the best way possible. After a brief investigation, I noticed that the pilot light on my water heater had gone out. Is it worth it to try to relight it? A: It all depends on what caused the light to go out. It’s possible that the problem was anything as simple as a draft, a filthy pilot orifice, or a worn-out part—or that the extinguished pilot light was a symptom of something more serious requiring attention.
If you find yourself in this situation, leave your home and call the gas company!
(Please keep in mind that if your water heater has an enclosed burner chamber, you’re most likely out of luck as far as a DIY remedy is concerned; only a professional plumber should be able to reach an enclosed burner chamber.) Make an appointment with a proGet free, no-obligation repair quotes from qualified appliance experts in your area.
When you see your pilot light out, you can usually relight it.
The presence of a downdraft in a vent pipe on a windy day, or even the breeze via an open window, can be sufficient to extinguish a pilot light. It is common for water heaters to include identical relighting instructions, which are usually permanently mounted to the side of the appliance. Image courtesy of fotosearch.com Remove the access cover located at the bottom of the water heater in order to relight the pilot. Ensure that the “Pilot” position is selected for both the control knob and the water temperature knob.
Continue to keep the knob down for a full minute after the pilot is ignited in order to remove any remaining air from the line.
Depending on what happens after the pilot ignites, one of the following options should be considered:
- If the flame continues to burn, you’re good to go!. Simply replace the cover plate, turn the control knob to the “On” position, and set the desired temperature on the water temperature knob to return to the refreshinghotshower experience. Ensure that the pilot light does not flicker and goes out immediately after relighting by cleaning the pilot orifice. Gas flow is impeded by a clogged pilot light aperture, but the solution is straightforward. Shut off the gas to your water heater first, of course (look for a valve on the gas line that supplies the unit). Twist the pilot orifice fitting to the left, which is positioned behind the access cover, to release it from its mounting. After that, remove the orifice itself from the fitting by unscrewing it. Using a cotton swab moistened with rubbing alcohol, thoroughly wipe all surfaces of the fitting once it has been dismantled. As soon as you have completed the reassembling and reattaching of the fitting, relight the pilot light as previously specified. You should replace the thermocouple if you are able to ignite the pilot light but it goes out as soon as you remove the control knob from the pilot light control box. It is a safety device that shuts off gas flow if it detects that the pilot light is out
- However, if it becomes broken, it loses its capacity to regulate the flow of gas. This repair is a little more involved than the previous two, but a replacement is rather inexpensive—often costing less than twenty dollars
Connecting the control panel to the burner assembly, which is hidden behind an access panel, is this item that looks like a copper tube. Turn off the gas to the water heater before beginning any disassembly efforts. Remove the burner assembly from the control panel by detaching the thermocouple tube, the pilot light tube, and the gas supply tube using an adjustable wrench. The burner assembly should simply slide out of the way. (Tip: Because thermocouples come in a variety of sizes and kinds, bringing the broken thermocouple with you when purchasing a replacement is the most effective approach to ensure that you receive an identical match.) Replacing the broken thermocouple with a new one is followed by reassembling the burner assembly, reattaching the tubes, and relighting the pilot light in the manner indicated above.
Make an appointment with a proGet free, no-obligation repair quotes from qualified appliance experts in your area.
How To Light The Pilot Light on Your Hot Water Heater
If you have a gas water heater, it has a pilot light that must be kept lighted at all times. If you don’t, you’ll be without hot water for quite some time. If it does go out, don’t be concerned; re-igniting it is simple. Simply follow the instructions outlined below.
Before You Start
Grab a flashlight and a wand lighter to help you out. If you have a recent water heater, it is likely that it has an electric light integrated into it as well. Then, using your nose and ears, check for any leaks that may have occurred. If you notice any unusual odors or hear a hissing sound, don’t go any farther and call IT Landes in Harleysville, Pennsylvania right now. We’re specialists in everything related to water heaters, and we can come out right away to take care of any problem. Finally, look inside the device for instructions on how to turn on the pilot light, which should be located on the inner panel.
If this is the case, the actions that follow are typically relevant to the majority of water heater units.
Adjust the Temperature Control and the Gas Valve
Turn the temperature control down to “low” and turn off the gas valve for a few minutes to remove any leftover gas that may have accumulated in the appliance. Then, set the gas valve to the “pilot” position.
Find and Light the Pilot
Open the access cover and look for the pilot, which should be visible protruding from the control valve when the cover is closed. Grab the wand lighter and squeeze the gas valve to start the engine. Next, while the valve is still held in the closed position, ignite the pilot. For approximately 20-30 seconds, continue to hold down the gas valve before releasing it. The process should be repeated if the flame goes out, and the gas valve should be held down for 45 seconds to 1 minute.
Once the pilot light remains on, switch the valve from “pilot” to “on,” replace the access cover, and adjust the temperature dial to your chosen setting. IT Landes has been in the heating, ventilation, and air conditioning sector since 1929. We’ve achieved an A+ rating from the Better Business Bureau as a result of our dedication to client satisfaction. Aside from that, we were named winners of Carrier’s President Award for quality leadership and achievement in 2019. Whether you want assistance with your water heater, ducts, furnace, or plumbing, we are here to help.
7 Reasons Your Water Heater Pilot Light Keeps Going Out
Once the pilot light remains on, switch the valve from “pilot” to “on,” replace the access cover, and adjust the temperature dial to your preferred level. It is the year 1929, and IT Landes has been in the heating and air conditioning industry. We’ve received an A+ rating from the Better Business Bureau as a result of our dedication to client satisfaction and integrity. As a result of our quality leadership and performance, we were awarded the Carrier President Award for 2019. Whether you want assistance with your water heater, ducts, furnace, or plumbing, we are here to assist you.
What Is The Pilot Light?
The Pilot Light is the heart of your water heater, and it controls the flow of water.
Essentially, it is a little blue flame that produces heat by burning petroleum gas. There would be no heat and, hence, no warm water if this flame were not present.
So, What Are The Reasons Your Water Pilot Light Keeps Going Out?
Not only will we identify the potential issues, but we will also provide you with solutions to those issues. Please take notice of the following: Check to see whether your water heater is still covered by the manufacturer’s warranty. If this is the case, it should be returned to the supplier or manufacturer for repairs or complete replacement. Precautionary measure: To begin, shut off the main gas supply valve to prevent potentially fatal gas leaks. Wait 5 minutes for the heat and gas to dissipate before continuing.
1. An Unclean Pilot Tube
It’s a problem that practically all water heaters have at some point. Please don’t be concerned, your heater is in perfect working order. It’s simply a buildup of dirt. The Pilot tube is responsible for supplying gas to the pilot light in order for it to burn. if the tube becomes blocked with dirt or other particles, the flame will go out. It is possible that the tube is partially blocked and only supplying a little amount of gas for combustion—which explains why your pilot light keeps going out.
To gently clear the tube, use a thin needle to poke it with.
You must be patient during this process.
Place the container back where it belongs and turn on your water heater.
2. A Dirty Thermocouple
In the case of a water heater, the thermocouple serves as its brain. It is in charge of shutting down the gas valve when it detects that the pilot light has gone out. Because the pilot light produces an electric current, the thermocouple is activated when this current is present. It serves as a safety measure, preventing gas leaks from occurring. As a result, a filthy thermocouple might be the source of your water pilot’s inability to function properly. When a coating of filth and dust accumulates on the surface of a thermocouple, the electric current cannot reach it.
On a chilly Monday morning, there is no hot water.
To begin, shut off the main gas supply valve and allow the thermocouple to cool before proceeding.
3. A Kinked Thermocouple
As soon as you’ve finished cleaning, double-check the location of the thermocouple. Also, look to see whether it’s a little bent. The thermocouple must be placed close to the pilot light in order for it to receive heat and activate the gas valve. As a result of being too far away, heat will not be received and an electric current will not be generated. The thermocouple will determine that the pilot light has been turned out and will seal the valve, cutting off the gas supply to the house. The answer is as follows: First, turn off the gas and turn off your heater, and then wait for the thermocouple to cool down before proceeding.
You’ll have to bend or straighten the thermocouple manually to get it back into position. To be effective, the blue flame must be placed close enough to the pilot light so it contacts or wraps around the blue flame.
4. A Broken Thermocouple
So, you’ve cleaned and straightened your thermocouple, but your water pilot continues to fail despite all of your efforts. You should be prepared to accept the possibility that your thermocouple is faulty at this point. Perform a diagnostic test with a multimeter on your thermocouple first, though, before you give up on it. If the voltage delivered by your thermocouple is significantly less than 20MV, then the device is almost certainly damaged and should be replaced immediately. The Solution: If the multimeter reading is near to, but not exactly at, 20MV, you can adjust the thermocouple closer to the pilot light to save energy.
5. Flex Tube Issues
Flexible tube is a long tube that links the gas controller to the burner, which contains the pilot light, thermocouple, and other components. If the flex tube is broken or blocked, the gas will not be provided to the burner for combustion to take place. Flex tube failures, on the other hand, are not as prevalent as thermocouple failures. This is why you must first inspect and ensure that your thermocouple is in excellent working order before turning your attention to the flex tube. The Solution is as follows: Straighten any kinks in the flex tubing that have formed.
Leaks in the gas line will lower the amount of gas that reaches the burner.
6. A Faulty Main Control Valve
It’s possible that you’ll never run into this situation again. We recommend that you examine the pilot tube, thermocouple, and flex tube before attempting to modify or repair this piece of equipment. The Main Control Valve Unit has a very low failure rate. However, don’t count it out just yet; it’s possible that it’s the source of your water pilot’s incessant failure. Main Control Valve: This valve is in charge of regulating the gas and water pressures of the water heater. Your water heater’s heart and soul is the thermostat.
When the gas is ignited, the main valve is fully opened, allowing for a consistent stream of gas to be provided.
The following are signs of a defective main control valve:
- A malfunctioning pilot button that does not illuminate after being pressed
- A malfunctioning control knob
- When the water temperature exceeds the stated range, you will feel extremely hot water.
The solution: There is no way around a defective main control valve in this situation. However, despite the fact that there are specialists who say they can fix this, manufacturers highly advise against it. It is recommended that you replace the item to prevent incurring more expenditures and causing damage to other components of your water heater.
7. Poor Electrical Wiring
When it comes to electric water heaters, this is generally a concern. The fact that you should always engage a professional to install your water heater is one of the main reasons for this.
If your water heater suddenly stops working, this is the first indication of a defective electrical system. The Solution: Turn off your water heater as soon as possible and contact a professional. Please do not tamper with the electrical wiring system.
Our Final Word
If all of your methods fail and your pilot light continues to go out, it’s time to call in the heavy guns (the professionals). We’re aware. We’re aware. The services of technicians are not cheap, but at the very least you will have greater confidence in the repairs. In addition to that, we are all aware of the dangers associated with electricity and natural gas. Your safety is of the utmost importance. Did you find this information useful? Check out Why Are Trane HVAC Units So Popular? for more information.