How to Light a Water Heater Pilot Light
Previous Post Next Post When a water heater pilot light goes out, it usually means that a natural change in gas pressure extinguished the flame.The main sign that a pilot light is out is one that everyone dreads: The water won’t get hot.It’s important to know how to light your water heater’s pilot light so you can get the flame going again as soon as possible, not only to get your hot showers back but also to make sure no gas gets accidentally released into the house in the event of a broken flame sensor.It’s important to follow the instructions on your water heater; instructions vary from make and model.But for most gas-powered water heaters, you can start by finding the gas shut-off valve on the water heater first, which is usually labeled clearly on the front lower part of the water heater.Turn the knob to “Off,” and then wait five minutes for the gas to clear before you follow these steps:
- Open the door or cover that provides access to the pilot light. In most cases, this will be positioned under the gas valve
- however, some water heaters will just have an open gap where you can see the pilot light burner instead.
- Locate the burner within the container using a flashlight or a headlamp. It will be reached by two little gas tubes. You’ll want to keep an eye on it while you’re at work.
- Turn the gas knob to the ″Pilot″ position and push and hold the button. This will initiate the flow of gas, allowing you to ignite the flame. Some water heaters feature a separate pilot mode button, which is commonly a red button, which you must push and hold in order to activate it.
- While keeping the gas pedal depressed, ignite the pilot light. Certain water heaters feature an igniting button that is red or black, while others must be lighted manually with a long lighter
- some models include a red or black igniting button.
- Maintaining pressure on the gas knob or button for a full minute after the flame is ignited is critical. Then slowly release it while checking to see if the light is still on.
- Turn the gas knob to the ″On″ position and listen for the unmistakable ″whump″ or whooshing sounds that indicates the main burner has ignited.
- Enjoy your hot shower when you’ve replaced the lid.
Despite the fact that a single extinguished pilot light is normally caused by a natural fluctuation in gas pressure, recurrent faults suggest a more serious problem with the water heater itself.The most typical problem that causes repeated pilot outages is a filthy or bent thermocouple, which is a thin copper wire and rod that detects the presence of a flame and immediately switches the gas off when it detects a lack of flame detection.
What is a Thermocouple?
A thermocouple is sometimes referred to as a flame sensor in contemporary water heaters because of the way it detects flames.Your thermocouple is most likely twisted, filthy, or damaged if the pilot light continues to go out after you have completed the above-mentioned lighting procedures.For those who find that their pilot light is twisted and not near the burner, they may simply turn off the gas, shift it over, and attempt lighting the pilot again.It may be necessary to clean the water heater gas valve and the main gas line near the heater if this does not solve the problem.Remove the three nuts that hold the thermocouple and the two gas tubes to the valve and set them aside for later use.The burner is typically simple to remove by simply sliding it out.
Clean out the burner ports with a vacuum, and then use a microfiber cloth and steel wool to clean the tip of the thermocouple.If this doesn’t solve the problem, you may get a new thermocouple for less than $15 at any hardware store or home improvement center.If your water heater is causing you more issues than you can manage, or if you’re ready to upgrade to a more energy-efficient one, you may call your local Mr.Rooter Plumbing for help restoring hot water to your home.Hundreds of qualified specialists work for us all across the country, and hot water heaters are only one of the plumbing and water appliances that we like repairing and upgrading the most.
- The use of hot water is simply one component of a great showering experience.
- Replace that sticky shower curtain with a bespoke glass shower door from Glass Doctor, a sister company in the Neighborly network of reputable home service providers, to let in more light, make your bathroom feel larger, and create the shower area of your dreams.
- Previous Previous post: Previous post: Next post:
How To Relight the Pilot Light in Your Gas Hot Water Heater
When the hot water heater in your home fails, everyday duties such as showering, laundry, dishwashing, and other household chores come to a grinding halt.If you have a gas-powered hot water heater, it is possible that the pilot light has gone out, which is the root cause of the problem.In most circumstances, if you relight the pilot, you should be able to go back into the air again.In this post, we’ll demonstrate how simple it is to complete the task yourself.
What does the pilot light do?
The pilot light of your gas hot water heater is a tiny, continuously burning flame that serves to start the burner of the appliance.To put it another way, if the pilot light goes out, the unit will be unable to heat water.It is possible for a pilot light to be extinguished for a variety of causes, including something as simple as a short stoppage in the gas line or an air bubble in the gas line.Warning: If you smell gas at any stage throughout the process, leave the area immediately and contact your energy supplier as soon as possible.
Steps to relight the pilot light.
- Remove your foot from the gas pedal. Find the gas shut-off valve on your hot water heater and turn it off. The knob should be labeled in a clear and understandable manner. Turn the switch to the ″Off″ position and wait 5-10 minutes to ensure that all of the gas has been expelled.
- Locate the pilot light access point. Most of the time, this will be under the gas valve.
- To locate the burner and two gas tubes, open the pilot cover (if one is present) and use a flashlight to peer inside the hole to locate the burner and two gas tubes
- Return to the gas valve and turn the knob to the ″Pilot″ position. By pressing the knob all the way down, you will begin to flow gas to the pilot. There are certain hot water heaters that include a separate pilot button
- if this is the case, press that instead.
- While maintaining control of the knob or button, reach into the access and ignite the pilot with an extended lighter while still keeping it down.
- Once the pilot light comes on, keep the knob/button down for about one minute. Release the knob/button carefully after that period of time, and make sure that there is still a flame emanating from the pilot.
- Return to the gas valve and turn the knob to the ″On″ position. You should hear a popping sound, which indicates that the main burner is starting.
- After giving the heater enough time to restart, replace the access cover and inspect the hot water supply.
What happens if the pilot light goes out again?
- The fact that the pilot won’t light or that it keeps going out is a clue that you may be experiencing another problem with your hot water heating system. The most typical issue we encounter is a thermocouple that is twisted, fractured, or filthy (also called a flame sensor). Because the typical service life of a hot water heater is 12-15 years, it may be a wiser investment in some situations to replace the unit rather than spend money fixing your existing unit. Give Reichelt Plumbing Inc. a call at (219) 322-4906 if your water heater isn’t heating up as much as it should. Our professional plumbers will come out to your house and inspect the situation before recommending the best course of action to restore hot water flow. The date has been set for April 30, 2020
- the category is Water Heaters
How to Light a Water Heater
Article to be downloaded article to be downloaded You may see cold water flowing from your hot water faucet if you reside in a home that has a natural gas water heater.This is a good indication that your pilot light has gone out.It is not necessary to hire a professional in most circumstances; you will have hot water again in a matter of hours if the pilot is re-ignited correctly.While having your water heater’s instruction manual on hand is a good idea, it is not fully required because most gas water heaters need a similar process for relighting the pilot light, as described in this article.
1 Make that the pilot light is working properly.You will most likely need to remove a tiny panel at the bottom of the tank, known as an access panel, in order to determine whether or not the pilot light is truly turned off.If you do not see a little flame flickering, this indicates that your pilot light has been turned off.Depending on your water heater model, it is conceivable that your panel is not detachable and that you must observe your pilot light via a transparent window.In this instance, if you are unable to see a flame burning through the glass, your pilot light is not working properly.
- 2 Check to see whether there is any gas leaking. Never attempt to restart your pilot light if there is gas leaking from your water heater, as this is highly harmful to both you and your property. Instead, call 911 immediately. To check for leaks before attempting to relight the pilot, perform a basic smell test on the cylinder. Standing near to your water heater, sniff the air to see if you can notice any strange aromas. After that, get down on your knees and smell around any valves on the front and sides of the tank. Naturally, natural gas has no odor. To make it noticeable to humans, gas companies add an ingredient known as mercaptan to the mixture. The smell of leaking gas is similar to that of sulfur or rotting eggs.
- If you detect the presence of gas in either of these locations (even if it is a faint odor), do not attempt to relight the pilot. Remove yourself from the vicinity of the water heater and contact your gas provider immediately
- they will advise you on what to do next.
- Also, keep an ear out for hissing sounds near the water heater, which might indicate a gas leak.
- Promotional material
- 3 Instructions may be found on the inside of the door panel of your water heater. Detailed instructions for your specific water heater model may be available here, and following them may assist you in the process of relighting the pilot for your unique water heater. Advertisement
- 3rd-party advertising Instructions may be found on the inside of the water heater’s door panel. Specific instructions and specifications for your particular model may be included below, and they may be of assistance to you in the process of relighting the pilot for your particular water heater. Advertisement
5 Gather any lighting items that may be required.You will need to obtain a long-reach ″wand″ lighter or fireplace matches to relight the pilot on an older design water heater.Avoid attempting to relight a pilot with a conventional matchstick or a small cigarette lighter since doing so will force you to place your fingers in a small, tight position too near to the open flame, putting you at risk of being burnt.
Gather any lighting items that could be required.If you have an old-fashioned water heater, you will need to obtain a long-reach ″wand″ lighter or fireplace matches in order to relight the pilot light.Never attempt to relight a pilot with anything other than a matchstick or a small cigarette lighter since doing so will force you to place your fingers in a small, tight position too near to the open flame, increasing the risk of being burnt.
1 Turn the gas valve to the ″Pilot″ position and press the button on the valve. It is necessary to do this in order to initiate the flow of gas into the tube that supplies the pilot light. Find a red control button near the gas valve on your water heater if the gas valve on your water heater does not press down properly. Keep your finger on this button.
- 2 Light the pilot burner with a match. The pilot gas valve or the red button will be held down with one hand while the other hand will be used to swiftly light the pilot. To use this button, make sure you have a new model water tank with a built-in ignition switch installed. You should be able to hear a clicking sound until the pilot burner comes on. If you have an old-fashioned heater, ignite the pilot burner with a wand lighter or match and wait a few minutes.
- Because you will be using one hand to push the valve/red button while using the other hand to ignite the pilot, you may require the assistance of another person to carry a flashlight for you if you require additional lighting. Make an effort to get assistance in advance so that you do not go halfway through a procedure only to be forced to halt because you are unable to see what you are doing
- 1 Minute after the pilot light has been ignited, keep the gas valve or control button down by pressing it down one more time. This will heat the thermocouple, which is a sensor that turns off the gas when the pilot is not lit.
- 4Release the valve knob/control button to complete the process. After a minute, open the valve and press the control button to check if the pilot light is still on.
- 5Remove the access panels and replace them. When checking to see if the pilot light is still lit, replace the access panel (if you had to remove it first) to ensure that no flames escape into your home.
- 6Restart the main burner. Turn the main gas valve back to the ″On″ position and set the temperature control to the appropriate temperature. The main burner under the tank should be turned on and the water in the tank should begin to heat. Caution: When turning the knob to ″on,″ be careful to keep your head away from the burner area.
- 7Set the thermostat to the appropriate temperature. Remember not to heat the water to a boiling point, since you might scald your hands or body accidently when washing or bathing. The Consumer Product Safety Commission recommends a temperature of 49 degrees Celsius (120 degrees Fahrenheit). Advertisement
- Question Add a new question Question How can I start a gas heater that is more recent in design? Look up your model number and get in touch with the manufacturer for more detailed information. For the most part, the only difference between a current heater and these instructions is that newer units include an electronic igniter (you simply press a button and a spark is produced) for lighting the pilot. What do I name the gadget that I use to ignite the pilot’s engine when I press a button on it? It’s referred to as a ″spark igniter.″
- Concerning the Question What should I do if the pilot light on my water heater keeps flickering on and off? It is likely that you will have to replace it. You can also get in touch with a supplier or even the business that made your water heater.
- Concerning the Question What should I do if the pilot light won’t remain lit for whatever reason? The most likely cause of your problem is that your thermocouple has to be repaired or replaced. A pilot light is a short copper tube that connects your water heater’s controls to the pilot light and has an end that sticks into the flame. Whenever the pilot light heats up the tip, it creates electricity that is detected by the control box, which allows it to determine that the pilot light is on. A new one is simple to install, and you can pick one up at any home improvement, plumbing supply, or hardware shop. Take your old one with you so that you may acquire the right measurement. A little bit longer is OK, but not typically much shorter
- Question When I press the pilot button, how long should I hold it down before pressing the little red ignitor button beneath it? It takes around 5 seconds. Question: Can you turn it back on and change the temperature? So, what should I do if the pilot light won’t turn on for whatever reason? Continue to try while keeping an eye out for any signs that there is gas coming through (usually by smell). The likelihood is that the regulator is faulty and that it will need to be replaced. This is also something that may be accomplished by oneself.
Inquire about something There are 200 characters remaining. Include your email address so that you may be notified when this question has been resolved. Advertisement submissions are welcome.
- If this procedure does not provide results, check to see that the pilot light’s base is not filthy or blocked. If it is, clean it well and repeat the process after 10-15 minutes. You may also try holding the valve/control button for an additional 30-45 seconds after the pilot light has been ignited.
- If this technique does not work, it might be due to a lack of gas pressure or a defective gas valve. If you are unable to ignite the water heater despite many efforts, contact an appliance repair person, a plumber, or your gas provider.
- You may have a faulty thermocouple if the pilot light does not come back on after being re-lit or if it goes out soon after being re-lit. It is possible to see the thermocouple in the pilot light flame region because it extends from the temperature control into the flame area.
- They are reasonably priced, and you can do the installation yourself.
- Thank you for submitting a suggestion for consideration! Advertisement If you detect the scent of gas anywhere in your home, contact your gas provider right once. Even a ″little smidgeon of gasoline″ is too much.
- Do not re-open the gas valve until you have completed the replacement of the access panels. It is possible that a flame will come out of the water heater if this is done.
About This Article
Summary of the Article Set the temperature control to the lowest setting and turn the gas regulator valve to the ″Off″ position to begin lighting an electric water heater.X Then, by adjusting the gas valve to the ″Pilot″ position and pressing down on it, you may begin to pump gas into the system.After that, press the red ignitor button, which is located near the gas valve, to ignite the pilot burner.Hold down the pilot button for 1 minute longer than you think it should be and check to see whether the pilot is lit.If it isn’t, go back and repeat the process until it is If this is the case, flip the gas valve back to the ″On″ position and adjust the temperature to your liking.Continue reading for helpful hints on how to prepare for and light your water heater.
Did you find this overview to be helpful?The writers of this page have together authored a page that has been read 389,137 times.
Water Heater Pilot Light Out In San Francisco, CA? Here’s Why It Happens and What You Should Do!
An issue that can arise with older water heaters is the loss of the pilot light flame, which is one of the most prevalent concerns. When this occurs, your burners will not light, and the water in your house will be ice cold as a result. The reason why your water heater’s pilot light can go out and what you should do if this occurs to you will be discussed today.
Why does a water heater’s pilot light go out?
- Here are a few of the most typical reasons why water heater pilot lights go out in the first place: A defective thermocouple was discovered. When your pilot light is turned on, your thermocouple is responsible for detecting it. If the thermocouple detects that the pilot light has been extinguished, it automatically cuts off the gas supply to the flame, preventing any potential safety hazards with your water heater. Even if the pilot light is burning properly, thermocouples can become faulty over time and cause the gas supply to be cut off. A bent or filthy thermocouple might cause this to happen. Along with regular failure, your thermocouple may suffer from dirt accumulation or the device may become twisted away from the flame of your pilot light, among other things. In either instance, the thermocouple will have a more difficult time sensing your pilot light, and it will shut off the gas supply to the flame
- the flame has been extinguished. If your water heater does not have a sealed combustion chamber, it is possible that the pilot light will be blown out as a result of a powerful draft passing close to your unit.
- There is insufficient flammable air. There is insufficient flammable air. If your water heater is placed in a utility closet or another area where it is lacking in combustible air, it is possible that the pilot light will not illuminate. A build-up of Carbon Monoxide, which can be fatal, could result as a result of this circumstance.
What should you do when your water heater’s pilot light goes out?
Even if this is the first time this has occurred to you, or if it hasn’t happened in a long time, you can attempt to relight the pilot light on your water heater by following these instructions.For specific information on how to do this with your specific water heater, contact Cabrillo or see the owner’s handbook for your device.Generally speaking, the procedure will look something like this: 1.Reduce the temperature on the thermostat to the lowest level.Switch the on/off/pilot switch to the ″pilot″ position to begin.3) Remove both the outer and inner panels in order to have access to your pilot light.
4.Using a long lighter or match, start the flame while holding the pilot button pressed down (some water heaters will not have a pilot button and can be lit without pressing anything) 5.Once the flame has been ignited, press and hold the pilot button for about 60 seconds to verify that the flame remains lighted and is blazing brilliant blue throughout.6.Turn the knob to the ON position after adjusting the temperature to your liking.
- We propose that you set it to ‘A’.
- Install the access panels and reset the thermostat to its default temperature setting.
Contact Cabrillo if your water heater’s pilot light continues to go out
If your pilot light goes out on a regular basis, or if it is not blazing bright blue, call Cabrillo for assistance.The issue is most likely something similar to what we discussed previously (such as a malfunctioning or filthy thermocouple), and it will require the services of a professional plumber to be resolved.Please feel free to contact Jerry Kelly, a plumbing, heating, and air conditioning contractor serving the Bay Area, if you have any concerns regarding what to do if your water heater’s pilot light goes out or if you’d like to have a plumbing system serviced or installed in your house.What is causing the leak in my water heater’s relief valve?» What is causing my pipes to ratchet when I turn on the faucet?
What Causes A Pilot Light To Go Out?
The majority of modern gas furnaces are ignited by an electronic ignition; however, older furnaces are likely to be equipped with a standing pilot flame, which is used to kick-start the heating system when the furnace is first turned on.For gas burners, a standing pilot light (in which the flame remains burning at all times) is used to function as a tiny igniting flame for the gas burner.When the pilot light on an older furnace goes out, it is a typical cause of the furnace not being able to run.But why does this happen in the first place?In this article, you will learn about some of the most typical faults that can cause a pilot light to go out and eventually a system shutdown.
Age & Condition Of Heating System
If your gas or propane furnace has a standing pilot light, there’s a strong likelihood that it’s been in operation for more than 20 years. Because of the age of the system, numerous parts and components are likely to have grown dusty, worn, and inefficient over time; any combination of these elements malfunctioning might result in the loss of the pilot light in the system.
Cracked Heat Exchanger
A fractured heat exchanger is something that we frequently encounter in older heating systems, and it is a typical cause of the pilot light going out in these systems.Simply said, a crack in the heat exchanger will have an affect on the air pressure and venting inside the combustion chamber, which will have an impact on the flame inside the combustion chamber.Depending on where the fracture is located within the heat exchanger, air can be forced into the heat exchanger and onto the flame.
Gas Valve & Gas Supply Issues
The pilot light must be fueled by a consistent supply of natural gas or propane in order to remain illuminated.If there is a problem with the gas valve that delivers the gas to the flame, whether it is unclean or faulty, it can result in the flame going out completely.It’s also conceivable that your gas supply has been insufficient or has ran out completely, which will also result in the flame going out.
The thermocouple in your heating system is a safety device that determines whether or not the pilot light in your furnace is illuminated or not.It is placed extremely close to the flame, and when lighted, it instructs the thermocouple to keep the gas line open.A filthy or defective thermocouple will frequently cut off your gas supply inadvertently, causing the pilot light to go out and your furnace to cease working.
Improper Venting & Airflow
An out-of-service pilot light may be caused by a gust of wind or a gust of air simply blowing it out of the fixture.If this occurs, there might be a problem with the way your flue pipe is configured or with the way your system is venting.What Are the Risks of Lighting Your Own Pilot Light?It doesn’t matter what caused your pilot light to go out; many homeowners aren’t sure if it’s safe to re-light the pilot light themselves.If you are dealing with a gas-related issue, it *might* be safe to re-light your pilot light; nevertheless, we always recommend having this done by a professional in these situations.This process may be performed safely by an expert HVAC service specialist, who can also assist in determining the cause of the system failure in order to prevent a system breakdown in the future and to assure the safe operation of your system.
Are you ready to make the call for assistance?Our team will be delighted to assist you!To obtain a free estimate, please click here.To request service, please click here.
How To Relight Your Furnace Pilot Light With Three Simple Steps
It’s every homeowner’s greatest fear to have their furnace go out abruptly in the middle of winter.You could be lucky, though, and find a remedy that is reasonably simple and easy, such as relighting the pilot.There are various causes for pilot lights to be extinguished, the most frequent of which are dirt accumulation surrounding the pilot light and a defective thermocouple (thermocouple that does not work).If the pilot light on your furnace has gone out, follow the manufacturer’s instructions or reset the system to re-ignite the pilot light.
3 steps to relight your furnace pilot
- Locate the sticker that contains the directions for lighting the furnace. If you are able to readily understand the directions on the sticker, make sure you adhere to them. If this is the case, go to step 2.
- Locate the pilot light as well as the ″on/off″ switch for the furnace. Most of the time, they are placed near the bottom of the furnace. IMPORTANT: When finished, turn off the light switch and wait FOR AT LEAST 5 MINUTES to allow gas from within the furnace to dissipate. While you’re waiting, look for the ″reset″ button on your keyboard. The location of this button will be important when you get to step 3
- set your knob to ″Pilot″ and hold down the ″Reset″ button for a few seconds. Bring the flame close to the pilot aperture by using a long lighter or a long match. This should cause the pilot light to come on. Once the pilot is lighted, you can depress the reset button to turn off the ignition. At this moment, the pilot should continue to operate.
A few pro tips to keep in mind:
Never attempt to start a pilot light in a furnace that has not been turned off first. This has the potential to cause significant personal harm or property damage. Prior to attempting to ignite the pilot light, it is critical to allow at least five minutes to elapse after the furnace has been turned off.
Make sure to keep your hands as far away from the flame as possible while igniting the pilot. Lighting a pilot light using a long-barreled lighter or a long matchstick is the most effective method of doing so. When working with an open flame near your furnace, exercise extreme caution!
It’s possible that cleaning the area surrounding the pilot light will help if lighting the pilot doesn’t work after a few tries of this procedure. It is possible that a buildup of dirt or debris will cause the flame to be extinguished or that it will be unable to light at all.
Don’t forget the thermocouple
A thermocouple that is not working properly is another major source of pilot light difficulties.If the pilot light ignites but then goes out after pressing and releasing the ″reset″ button, this is a good indication that there is a blockage in the pilot tube, and this should be addressed immediately.We recommend that you hire an HVAC expert to repair your thermocouples because they are difficult to change on your own.
Furnace repair in Buffalo, MN
- Are you still experiencing problems? Alternatively, it is possible that there is an underlying issue that has to be addressed. In order to put an end to your furnace pilot light problems, contact the professionals at DeZiel Heating & Air Conditioning. Call (763) 684-3965 to schedule an appointment right away. Published on January 19, 2021
- in the category of Furnace
- 0 comments.
How Do I Relight My Pilot Light?
Return to the Blog The pilot light of the furnace ignites the burners and initiates the heating process in the furnace.Pilot lights were formerly standard on all gas furnaces, however modern systems do not necessarily include pilot light ignition devices, as was the case with older models.Some contemporary furnaces, on the other hand, are equipped with electronic ignition mechanisms.The loss of your pilot light will result in your furnace being unable to create heat because the burners will not be able to ignite.The majority of the time, homeowners can relight the pilot on their own.The following is a step-by-step tutorial on how to relight the pilot light on a gas furnace.
How to Relight a Pilot Light: 5 Steps
1. Find the pilot light assembly and its reset switch.
The pilot light of a furnace is typically located at the bottom of the device, controlled by a knob. Typically, the knob is labeled with three different settings:
If you are unable to locate the pilot light and reset switch on your furnace, consult your furnace’s owner’s handbook for a schematic indicating their placement. If you are unable to locate the hardcopy handbook, you can look for it on the manufacturer’s website.
2. Set the reset switch to off.
Turn the knob all the way to the ″Off″ position. You should be able to adjust it with your fingers without difficulty. The gas flow is halted as a result of this.
3. Wait a moment.
After turning off the pilot, it’s crucial to give it some time to cool off completely before attempting to re-light it. This allows the gas to drain from the chamber, preventing you from accidentally igniting additional gas while re-igniting the pilot. A minute to two minutes should be plenty time.
4. Relight the pilot light.
Turn the knob to the ″Pilot″ position and allow gas to flow to the pilot light. Light a lighter or a match, and then press the reset button on the remote control. Keep your flame close to the opening of the pilot light. To ensure that the pilot light continues to burn steadily, keep the reset switch depressed. Then press and hold the button for a few seconds.
5. Observe the furnace.
Once the pilot light has been re-ignited and the reset button has been depressed, your furnace should begin to operate on its own.For a few moments, keep an eye on the pilot light to make sure it remains lit.Check the surrounding area for drafts or other air sources that might have caused the pilot light to go out at the start of the experiment.Don’t hesitate to call an expert HVAC contractor at Parker’s Heating & Cooling if you are unable to relight the pilot light or if you are uncomfortable executing the instructions above on your own.Call us at (615) 355-9137 or send us an email!If you need assistance with your pilot light or any other furnace repair for your home or business in or around Smyrna, TN, we’re here to help you.
Contact us now.We also welcome you to take advantage of our unique offers and become a member of our Comfort Club, which allows you to save money while still receiving dependable, high-quality business and residential HVAC services across Rutherford County, TN!
Is The Pilot Light On My Water Heater Out? How Do I Relight It?
- Showers that are too cold? Status indicators that blink? When there should be a flame, there isn’t one. All of these are indications that the pilot light on your water heater has gone out. Fortunately, that is a quite simple repair. In this tutorial, we’ll go over the following topics: How to determine whether or not your pilot light is working properly
- How to get it to work again
- How long do you think it will be until you get hot water again
- What is the reason for it continuing to go out?
Meanwhile, if you have any concerns or want assistance, please contact Broadley’s by phone or email. Even when we distance ourselves and practice social distancing, Broadley’s relies on phone conversations and virtual consultations to answer inquiries and obtain further information about our products and services.
Signs your pilot light is out
- You can determine whether your water heater’s pilot light is out by looking at the water temperature, the blinking light or error message, and the lack of a visible flame.
Your Water Is Cold
If you’ve reached the point where you’re only getting cold water, start troubleshooting by checking the pilot light on the faucet.Of course, there are a variety of additional possibilities for why you aren’t getting hot water.The most apparent example is if you’ve recently used a lot of water and completely depleted the tank.However, if this is not the case, the pilot light should be checked first.If that is not the case, you may be dealing with a more serious issue.But, with any hope, it will be a simple remedy.
Blinking Light or Error Message
The first thing you should do is look at the control panel of your equipment.It’s normally located at the bottom of the device, with one or two lights illuminated.If there is an issue with your model, that light may remain on, flicker, or change colors to alert you to the situation.If you have a handbook, look through it.Generally, though, there is a sign or key directly on the heater that tells you what the different lights represent and how to use them.If your light shows that the pilot light is not working, you’ve found the source of the problem.
You Can’t See the Flame
The final stage is to conduct a visual inspection.Double-checking is still recommended, even if you are utilizing the status light.You’ll also need to know where to seek for the items later on in the game.A space at the bottom of the unit should also be there so that you can view what’s going on beneath the unit.That’s where the flame should be placed, right?If you’ve been there previously and saw the pilot light on, it’ll be much easier to locate the location.
However, if you don’t see anything and the status light shows that it is not working, you’ve identified the source of the problem.
How to Turn Your Water Heater Pilot Light Back On
It’s simple to re-ignite the pilot light on your water heater.But first, make sure there isn’t a gas leak.The lighting of a flame in the presence of a leak might result in an explosion.Fortunately, this is straightforward: Check the area surrounding the pilot light to check sure there isn’t any gas coming from it.If you understand what I’m saying, you can proceed.Now, various models will have slightly varied approaches to exactly how to accomplish this.
However, the general concept remains the same.Check that access panel one more time.You’ll notice a knob with temperature settings, as well as a notch with the words ″Pilot″ or ″Pilot Light″ written on it.Look for it, as well as the ignitor button.It’s normally located in the middle of the panel.
- Turn the knob to ″Pilot″ and keep it there while pushing the ignitor.
- A click, as well as a ″whooshing″ sound, should be heard as the mechanism engages.
- If you look through that space, you should be able to see the light on.
How Long Will It Take to Get Hot Water Again?
It takes an ordinary gas heater between thirty and forty minutes to heat a full tank of water on the lowest setting.The precise timing will be determined on the available capacity.For the sake of comparison, consider the following: A typical electric heater takes at least an hour, and in some cases up to 80 minutes, to reach operating temperature.In the case of solar-powered equipment, the same holds true.Tankless systems, on the other hand, do not require a pilot light or a waiting period before providing hot water – ever.In contrast to traditional tank systems, tankless systems do not store warm water in a tank until you need it.
In place of it, they heat the water as soon as you turn on the faucet.They’re becoming increasingly popular for coastal homes, particularly those with many apartments or where a large number of people are bathing at the same time after a day at the beach.
Why Does My Pilot Light Keep Going Out?
The presence of dirt surrounding the pilot region and an issue with the thermocouple are two major causes of the pilot light not working properly. We’ll take a look at each of them individually.
The area around the light is dirty
Dust and dirt surrounding the pilot light, particularly around the pilot light aperture, might cause the pilot light to continuously go out. The hue of the flame will indicate whether or not there is an issue.
A flame that is a continuous blue cone indicates that everything is in working order. If, on the other hand, the flame is orange or yellow and waving, this indicates that dirt and other impurities are being burned. At that moment, the flame isn’t hot enough to properly heat the contents of the container. Additionally, it increases the likelihood of burnout.
A weak flame will not heat the thermocouple, which is a safety component on your equipment and will not function properly.The thermocouple has the capability of closing the circuit that supplies gas for combustion.In order for your heater to function properly, gas must flow into it and burn in order to create heat.However, if anything isn’t operating properly, the chamber might get overfilled with gas, which can then seep into your home.Consequently, the pilot light keeps the thermocouple warm, which helps to maintain gas circulation.If the pilot light goes out, it does not heat the thermocouple, which then closes to prevent unwanted gas from accumulating within the house.
It is possible that if the thermocouple is clogged or worn out, it will not respond to heat and will instead shut off the gas supply.When there isn’t enough gasoline, the pilot light goes out.
Water Heater Repairs in South Jersey
If the pilot light on your water heater keeps going out on a frequent basis, or if you’ve observed any other problems, contact or email us at Broadley’s to schedule an appointment.
Assorted Water Heater Problems, Commonly Reported HVAC Problems
- Hannabery HVAC is the owner of the copyright. All intellectual property rights are retained. Please do not attempt to fix your hot water heater on your own unless you are certified to do so! The information provided below, which pertains to a variety of water heater issues, is predicated on the assumption that the water heater was properly installed and was performing properly prior to the occurrence of any difficulties. These are only broad instructions that address the most frequent water heating issues, with the goal of assisting you in becoming a more knowledgeable customer. Help! There are a variety of issues. 1. There is no hot water because of the gas. Water heaters are used to heat water. Removing the inner and outer burner access covers and checking to see if the pilot light is lighted is recommended. * Caution: Most new water heaters do not employ standing pilots any longer. To light the gas, they employ an electrical ignition system. Don’t make the mistake of attempting to manually start an electronic ignition system. If the pilot light is not illuminated, the following will occur: Follow the directions on your water heater’s pilot light to see if you can re-ignite the flame. Alternatively, you may follow the instructions here.
- This might be because the pilot light is clogged or that the gas is not reaching the water heater, which could indicate a clogged or blocked pilot line or orifice. It is necessary to contact a service technician if the pilot light will illuminate but will not remain illuminated when the gas valve control is removed. The problem might be caused by a faulty or loose thermocouple, as well as a malfunctioning gas control valve. Examine and confirm that the thermocouple connection to the control valve is secure.
- If the pilot light is on, turn on a hot water faucet and let the water flow for a few minutes to cool the pilot light. Inspect to check if the burner is activated. If this is the case, continue to run the hot water for a few more minutes. The problem might be a faulty control valve/thermostat if the burner does not turn on after a few of attempts.
- Determine if the control valve knob is in the ″on″ position and not in the ″pilot″ position by turning it clockwise.
2.No hot water despite the presence of an electric water heater.In the event that your electric Hot Water Heater is not producing hot water, first check to see if the breakers are turned on.Without a malfunctioning upper element or thermostat, the most likely cause is that the high limit safety has been activated.Some water heaters are equipped with a reprogrammable safety switch located at the top thermostat.It is normally necessary to remove the upper access panel to do this.
* Caution: High Voltage connections are located behind access door openings.Before removing the water heater panel, be sure that all power to the appliance has been off at the main panel box.When removing the panel, proceed with caution and use a volt meter to double-check any electrical connections.Attempting anything like this should only be done if you are confident in your ability!Once it has been established that the electricity has been turned off, check to see if the red reset button has been pushed out.
- If this is the case, try resetting it; you should hear a click.
- After that, replace the panel cover and reset the circuit breaker.
- You should be able to hear the device begin to charge.
- Keep in mind that if the upper limit opens, it is typically due to a thermostat that has become stuck closed, and it will do so again, necessitating a new thermostat installation.
- Insufficient hot water – Check the thermostat setting; it may be set too low.
4.Insufficient hot water – Check the water pressure.Look for any dripping faucets.
- It’s possible that there is a problem with the dip tube.
- If the dip tube is damaged or has come off, incoming cold water will be sucked out of the hot water outlet without being heated by the hot water heater.
- You should keep in mind that you shouldn’t try to check this on your own!
- Other probable causes include blocked burners and low gas pressure, both of which would necessitate the need for a repair visit.
- Insufficient hot water recovery – This might be caused by sediment accumulation on the bottom of the water heater.
It is possible that flushing the water heater will assist.Among the other probable causes are insufficient combustion air, which can be caused by inadequate ventilation, and inappropriate burner operation.If you have this sort of system and you are running out of hot water, it is likely that the thermostat is set too low or that the system is malfunctioning.Another possibility is that the circulator or circulator relay has failed, or that the zone is air-bound and has to be purified.5 – Discharge from the TP/Relief Valve The relief valve will open if either the temperature of the water is too high or the pressure of the water becomes too high.Because there are no pressure relief valves or check valves between the water heater’s input and the water main, when the water is heated and expands, the increased volume of water just flows back into the water main, bypassing the water heater.
As a result, when there is an obstruction such as a check valve or a pressure reduction valve with a malfunctioning bypass, the increase in water volume has nowhere to go, and the pressure rises drastically as a result of the increased pressure.It is recommended that you install an expansion tank in your water line at the entrance.This will provide a place for the additional volume of water to go and will prevent the relief valve from opening.Another scenario is that the city water pressure has risen over the pressure limit established by the relief valve, causing the valve to open.
Installing an expansion tank can again assist in resolving this issue, at the very least in cases where there is just a slight to moderate rise in localized pressure.A considerable rise in pressure, on the other hand, will still force the relief valve to open.6.The pilot light will not remain illuminated – (Standing pilot models only) A draft might cause the pilot light to go out on occasion.Check to see that the burner access covers are securely fastened.
Other probable causes include debris in the gas line, loose thermocouple connections, or a faulty thermocouple, among others.For additional information on this issue, please see this link.Popping or banging sounds can be made by the water heater when scale accumulates at its bottom.
- This can cause a variety of noises to be made when the water heater is heating the water.
- Try flushing the tank with water.
- – Certain forms of bacteria can react with the magnesium anode rod, resulting in the formation of a rotten egg smell when hot water is used.
- Most of the time, cleaning the tank with chlorine bleach or replacing the anode rod with aluminum will resolve the problem.
- Leaking Tank – It is inevitable that tanks will leak!
- It’s an inevitable fact of life, just like death and taxes!
- Sorry, but there is no remedy for this!
- It is necessary to replace the water heater.
- Note that the material on this website is supplied without charge, and Hannabery HVAC does not accept any responsibility for any actions taken as a result of the information we offer.
- If this material is helpful, please keep in mind that these are only general principles, and that not all conceivable circumstances are addressed.
- A qualified expert should evaluate and repair your heating, ventilation, and air conditioning system.
How to Reignite Your Water Heater’s Pilot Light
Previous Post Next Post Your gas water heater’s pilot light has gone out due to a power failure.So, what do you do now?Use these ideas to understand how to swiftly re-ignite a water heater before you start picturing ice cold showers and mountains of dirty dishes and laundry on your hands.Continue reading for professional advice on how to get your water heater back up and running so that you can resume taking hot showers and doing your dishes as you normally would.
Do You Need to Learn How to Reignite a Water Heater?
- A water heater is typically seen as a household appliance that is out of sight and out of mind – at least until it ceases to function properly. It’s likely that you haven’t given much consideration to the sort of water heater you have in your residence. Here’s how to tell if you even need to restart your water heater in the first place. If you have an electric water heater, you won’t have to worry about re-igniting it. Electric water heaters do not use any gas or require the use of a pilot light. If the electricity to your electric water heater is out, you may be experiencing an electrical problem that necessitates the use of a professional.
- If you have a newer model water heater that is fitted with an automated pilot light, you will not have to relight the water heater.
- In the event that your gas water heater does not light automatically, you will need to rekindle it.
How to Reignite a Gas Water Heater in 7 Steps
Identifying whether or whether you have a gas-powered water heater should be the first step.Read the user handbook for information on how to relight the pilot light.Additionally, instructions for using a gas water heater are frequently placed on the outside of the tank.The following procedures should be followed if you do not have access to an owner’s handbook or if there are no instructions on the tank:
- Open the door or cover that is blocking the pilot light’s access if one is present. However, some versions will have an open gap where you can see the pilot light burning, which is normally positioned under the gas valve. This type of water heater does not have an open gap and so is known as a sealed burner assembly. Attempting to remove the lid is not recommended. In order to avoid the ignition of flammable vapors outside of the water heater, a sealed burner assembly or Flammable Vapor Ignition Resistant (FVIR) unit is used.
- Locate the burner with the use of a flashlight or a headlamp. There are two little gas tubes that run to the burner
- one is on the left and one is on the right.
- Turn the gas knob to the ″Pilot″ position and keep it there for a few seconds. This phase stimulates the flow of gas, which allows you to ignite the flame after it has been lit. If your model has a distinct button for pilot mode, push and hold it down
- if not, press and hold the button down until the pilot mode is activated.
- Light the pilot while maintaining control of the gas knob or button. The igniting button on your water heater may be red or black, or you may have to ignite it manually with a long lighter, depending on the kind you have.
- Continue keeping the knob or button down for a full minute after the flame is ignited, then gradually release the knob or button to ensure that the pilot light remains burning.
- When you turn on the gas, listen for a ″whump″ sound or a whooshing sound that indicates the burner is lighting
- if you hear neither, turn the gas off.
- Once the pilot light has been started, close the access cover to the pilot light.
Need Help with Your Hot Water Heater? Mr. Rooter® Plumbing Can Help
When it comes to getting the support you need with your water heater, it’s sometimes more convenient to resort to expert plumbing specialists.Your local Mr.Rooter Plumbing experts is available to assist you, whether you are having difficulty lighting the pilot or adjusting the water temperature.To arrange plumbing services, call (855) 982-2028 or submit an online request for an estimate.Do you require additional storage space in your utility room?Mr.
Handyman can assist you with this.Because they are a member of the Neighborly family of home service providers, you can rely on them to offer you with great service and craftsmanship.Previous Previous post: Previous post: Next post:
How to light a gas water heater
If you’re water won’t heat up, the pilot light on your water heater may have blown out.Lighting a water heater is simple, no matter what type you have.Most newer models of gas water heaters have a simple ignition switch.In just a few steps the water heater is lit, no problem.If you’ve moved into an older house, though, you many have the kind of water heater that needs to be lit manually.Here’s how to light both types of water heaters.
Do you have a manual water heater?
There is a straightforward technique to determine if your gas water heater is automated or manual. Take a look at the box that protrudes from the side of the water heater and has two distinct dials. Automatic vehicles will feature a little ignition button adjacent to the large On/Off/Pilot dial, indicating that it is an automatic. If it is a manual, there will be no button to press.
How to light an automatic water heater
When you turn off the gas, check for the knob that says On/Off/Pilot first, then turn it off completely.Ensure that the knob is turned beyond Pilot and into the Off position before continuing.Allow for a five-minute dissipation of any built-up gas that may be present in the system.It’s time to start the lighting procedure at this point.Make sure the water heat dial is set to Low and the On/Off/Pilot dial is set to the Pilot position.Then, while simultaneously pressing the igniter button and turning the On/Off/Pilot dial downward, turn the ignition switch on.
Allow the igniter button to be released, but continue to press the Pilot dial downward for about 30 seconds.You should hear a ″whoosh″ sound as soon as the gas is turned on.Taking the little door below the ignition box will reveal a small window through which you may peer to see whether there is an open flame within.If it is lit, conclude by closing the door and turning the dial from Pilot to On, as well as changing the water temperature dial from Low to the temperature you choose.To avoid gas accumulation, you must restart the process immediately if the pilot light is not lighted.
How to light a manual water heater
- To fire this style of water heater, I recommend using a long barbeque lighter like this one.
- In any other case, getting in touch with the pilot will be difficult.
- To begin, remove the plate that is located beneath the dial-equipped box on the side of the water heater.
- There may also be an inner plate that you will need to shift to the side in order to complete the installation.
- Following that, you should notice a pipe or pipes heading to a burner.
- Next, move the knob on the box labeled On/Off/Pilot beyond the Pilot position and into the Off position to complete the process.
- After that, wait for five minutes to allow any residual gas to disperse.
- Turn the water temperature dial to Low and the On/Off/Pilot dial to Pilot to complete the installation.
- While using one hand to push the On/Off/Pilot dial downward, use the other to ignite the barbeque lighter on the grill.
- Hold the barbeque lighter over the end of the pipe near the burner for a few seconds.
- The flame should be ignited immediately.
- Continue to press the Pilot dial downward for approximately 30 seconds, after which you will be able to switch it from Pilot to On.
- Finalize by placing the plates back over the burner hole and adjusting the water temperature control to your preferred setting.
Important: If the burner does not come to life within a few seconds, repeat the operation until the burner does.If you continue to do it for an extended length of time, gas can accumulate and produce an explosion.Is the energy efficiency of your home high?Here are five different methods to find out.CNET’s Guide to Smart Living is a one-stop shop for tips, techniques, and guidelines to help you live a more intelligent life.
How to Relight the Pilot Light on Your Water Heater
- Several factors might contribute to a pilot light on a water heater being turned off.
- The front of most water heaters will contain instructions on how to relight the pilot light, and this will usually be on the right side of the water heater.
- The first step is to turn off the gas to your water heater by turning off the gas control valve on the tank.
- Then follow these instructions to re-ignite the pilot light on your water heating system:
- Remove the access panel for the water heater
- Double-check to see that the gas valve is open (on most valves, this implies that the valve is in line with the pipe)
- Make sure that the gas control valve on the water heater is in the pilot position.
- Hold the knob on the front in and press it in.
- For a flame to emerge on the screen, hold down the ignitor button (the black square button below the knob).
- Keeping the knob pressed in until the indicator light starts blinking is recommended.
- Using the knob, adjust the temperature to your liking.
- The flame should be visible via the viewing window if you look closely enough. That indicates that your pilot light has been turned on. Although the gas control valve on your water heater may be different, the process of relighting it should be very similar. You may look up ″How to relight a″ on Google and fill in the blank with the name of the brand of your water heater to see what comes up. YouTube is another excellent source of information. Gas control valves come in a variety of shapes and sizes, and they might be installed on your water heater. Some further how-to videos on relighting the pilot light on a water heater with different gas control valves may be found at the following links. Style 1
- Style 2
- Style 3
If you are unable to relight your pilot light, or if it does light but continues going out on you suddenly, contact a plumber you can trust for assistance in determining what is causing the problem. All Posts Posted on August 25, 2021